No cool. Evaluated system and found compressor side of dual run capacitor to be out of tolerance. Rated at 45uf, actual was .40uf. Compressor was not starting. With approval from homeowner I replaced dual run capacitor under 5 year part warranty. No labor warranty. Washed condenser coil and checked operation. All amps and pressures are good. Required subcooling is 8 degrees +/- 3 degrees, actual subcooling was 10.1 degrees. System is operating normally.