TECHNICIANS REMOVED THE OLD UNIT AND REPLACED IT WITH A NEW CARRIER PACKAGE HEAT PUMP
Tech is servicing a Goodman heat pump.
Performed service and cleaning of Trane/ Coleman spit system.
Maintenance on 2 system split
Maintenance on two systems
Tech is performing annual tune up on two older style Goodman split system heat pumps.
Performing diagnostics on split heat pump
Replacing failed condenser fan motor on GOODMAN heat pump