I was very impressed with the service. He was very informative and extremely pleasant and fruendly
ESA 2 SYSTEM
Corrected wiring in air handler thst was preventing humidfier from working correctly.
Tech is servicing a Trane split system.
PTU 2 SYSTEM
ESA 1st VISIT
Inspected 2 Trane system for not cooling. Both systems are low on freon R-22, recommend replacement of systems.
Tech is servicing a mini split system.