Tech returned to preform approved repairs. Tech wired up primary float switch to low voltage side of furnace. Verified system was operating. Tech then replaced Run Capacitor on AC Condenser #3. Tech also replaced Dual Run capacitor on AC Condenser #4. Tech has attached pictures to invoice.
Techs preformed CMA FULL SERVICE on 5 split systems, 1 exhaust fan and 1 air makeup unit. The air makeup unit has voltage going to unit but fan motor is locked up and there is a bearing missing on blower shaft. Tech recommends replacing air makeup unit. Split System #3 is operating but compressor is operating at higher amps than listed on data label. Compressor also tested in the caution range, and unit is in need of Run capacitor. Tech recommends replacing system. All other systems are operating at this time, with only needing minor repairs on systems #4 and #5. Tech has attached estimates for these repairs to invoice. Also tech has attached system performance reports along with pictures to invoice. Maintenance staff informed techs that they had issues with ductwork leaking water around supply vents. Tech inspected supply vents that were under question and found vent did have water leaking from them but source of issue was not in AC system or ductwork. Supply vents have water lines ru