Great, professional and fast service. Very happy with Mike and Drew and the company as a whole! Thank you all!!
Excellent, prompt, and courteous service. Highly recommended.
Everything went perfect!
Nick again was prompt and very efficient in servicing our air conditioning unit.
Great as always
Nick has been to our home before and was familiar with our a/c and furnace. He knew what was needed to get it back in service and was here when he said he would be. Very pleased with him and the service we received.
Found unit with a bad blower motor will have to order oem blower motor on Monday Replaced blower motor
Found unit with no refrigerant added a few ounces and found a large leak from a hole in the condensor unit will need to be replaced gathered unit info condensor model and serial were not legible gathered compressor info as a substitute customer has no cooling at this time.
hot air coming from attic, once drywall repair is finished problem should n ot persist
advised customer to use thinner filters, system checks out great
Performed summer maintenance cycled all equipment needed checked all safety devices checked filter checked refrigerant charge cleaned condenser coil unit working within specifications all operations ok at this time. Customer also signed up for CM
Bad capacitor replaced also sprayed down outdoor unit told customer to change filter regularly system working with in specifications at this time mail invoice have no email
Found unit working within specifications all operations ok at this time. Customer billed service charge
Preformed summer maintenance checked all safety devices changed filter on one system other system filter dirty did not have right size told customer to change it system working with in specifications at this time
Performed clean and check on ac system checked temp drop tested and inspected all electrical components and controls rinsed and cleaned ac and removed leaves from the bottom of the unit all operations are normal at this time.
Preformed summer maintenance checked all safety devices changed filter system working with in specifications at this time customer wants invoice in mail
Performed summer maintenance cycled all equipment needed checked all safety devices checked filter checked refrigerant charge cleaned condenser coil unit working within specifications all operations ok at this time. Notified customer about rusty capacitor customer also renewed CM
Found unit with dirty air filter and very dirty condenser coils removed filter and cleaned condenser coils check system charge all operations are okay at this time
Found unit low on Charge and very high head pressure cleaned condenser coils installed stop leak and recharge unit with 3 lbs of R410A cycle system all operation are okay at this time
Found both units not working unit one was off on high head pressure due to a weak capacitor on the condenser fan motor replaced capacitor 2nd unit was not receiving a call due to faulty thermostat replaced thermostat and had to replace thermostat wiring so the thermostat can be powered by the unit
found thermostat blank when I arrived checked out furnace and control board had power check the connections reset control board and thermostat came on Checked all wire connections and could not find the problem or duplicated