I appreciate all the time the tech spent checking my AC. He said everything seemed fine which was good to hear. He also shared with me info I did not know about my AC. Thank you Jansen!
Nick was extremely professional and friendly ! Very knowledgeable !
Found unit with a bad capacitor, removed and replaced with a new capacitor, cycled unit, all operations ok at this time. Customer calling in to become a member during the week.
Found unit completely out of refrigerant and the compressor locked up, due to the age of the unit and price of repairs I quoted a new unit, not operating currently. Today bill to come off new unit.
Performed clean and check on a.c. noted that drain line was crushed qouted price for repair customer will contact me if they elected to do so all operations are normal at this time for a.c. system.
Performed clean and check on a.c. system unit leaking heavily due to improper installation of drain line by a separate company informed customer that existing drain line must be removed and replaced and a condensate trap installed. Also sold maintenance plan to the customer. Installed drain line and trap cycled system and confirmed proper operation continued clean and check found loose wire on contacter from compressor which I repaired all operations are now normal at this time informed customer there is some residual water around cabinet from the unit leaking that will dry in roughly 24 hours.
Checked unit found thermostat not wired correctly or set up right repaired system operation ok
Found unit with a bad capacitor, removed and replaced with a new capacitor, cycled unit, all operations ok at this time.
Found gas turn off to heater. Turn on gas cycled heater all operations are okay
Started a.c. changed filters supplied by the customer replaced uv bulb performed a.c. clean and check all operations are normal at this time.
Cleaned system check amp and voltage system in good condition
Performed spring maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed air filter, cleaned coil, found unit to be working within specification, all operations ok at this time.
Installed best thermostat under install warranty retrieved honeywell stat tested operation of system in heat and cooling mode all operations are normal at this time.
Checked unit found bad start capacitor replaced system operation ok at this time
Performed diagnostic testing on unit. Found unit had a bad capacitor. Replaced capacitor and checked operation. Everything working properly at this time.
Checked unit found unit freezing up due to clogged filtering takes 20/25/1 inch filter informed customer to replace also found drain line practically stopped up cut line and blown line out with drain gun checked charge system in good condition my see water for next couple days to!l all excess water runs through unit but should get better every day
Checked unitfound found return box still had water unitfound from leak pothole in box to rainwater system ok