Nathan cane after hours on a very cold evening when my furnace wasn’t working. He was friendly and patient. He was able to find out the problem, get it working for the evening, and gave information and a quote on what was needed to fix it long term. He took the time to explain the type of system I had, how old it was, and what options there would be when replacement was needed. I’m sure he had a busy night with calls, but took his time to help and explain things.
Our technician was very through and informative.
Nick Hursh was wonderful.
Nick was knowledge and pleasant to work with.
My furnace was evaluated, but the repair is scheduled for later today.
Nick does a nice job!
Started furnace and performed clean and check on Goodman gas furnace changed filter supplied by the customer inducer motor bearings are worn however motor is not effecting operation of the system at this time but did warn customer that motor could go out in the near future and they may want to consider replacing the furnace at that time given the age of the furnace.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed humidifier pad, found unit to be working within specification, all operations ok at this time.
Started furnace checked temp rise insured proper operation of the humidifier customer had already replaced pad left spare on site tested and inspected all electrical components and controls and cleaned flame sensor and condensate trap performed combustion analysis and found co was to high due to a small crack at the heat exchanger checked for co in air stream and found none informed customer that heat exchanger was failing and due to the cost of repairs and the age of the furnace highly recommended that customer replace the system customer had a quote made up from Mike on 8-03-17 Greg is looking into it and will contact customer with further details.
Rebuilt steam generator per Quote cycled system and found that the steam valve was not closing every time so replaced steam valve cycled unit and all operation are ok at this time
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, found unit to be working within specification, all operations ok at this time.
Performed clean and check on carrier gas furnace and heat pump customer wanted heat pump lock out raised set heat pump to lock out at 35 degrees. Changed filter performed clean and check on humidifier and showed customer how to set damper for winter or summer all operations are normal at this time.
Found furnace not working customer had change battery and did not get stat back on base properly cycled system all operation are ok
Found electric furnace with a blown low voltage fuse Tracked short in system to outside heat pump. heat pump has a bad Defrost board Unhooked low voltage at furnace to heat pump replace low voltage fuse customer now is running on backup heat I will call with price and Fallibility of the defrost board.
Installed inducer motor cycled furnace all operations are normal at this time.
Said they were having problems with 3 of the thermostats, found the batteries to be corroded in one and the batteries to be kinda loose in another, changed center thermostat to emergency heat as I think that system isn't keeping up at night cause colder than normal temps in the other areas, tested all operations and checked programming on all three thermostats and found no other issues, gave instructions to have them call back in tomorrow if nothing changed, all operations ok at this time.
Installed new Carrier fan coil and Carrier heatpump. Everything is working properly.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed oil filter and nozzle(1.10 80A), found unit to be working within specification, all operations ok at this time.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed oil filter and nozzle (1.20 70B) , found unit to be working within specification, all operations ok at this time
Started furnace changed filter performed clean and check on furnace activated humidifier solenoid valve is leaking heavily and was not able to repair informed customer they need a new solenoid valve customer may also need copper piping replaced. Humidifier not under contract. Returned and replaced solenoid valve and performed clean and check on humidifier replaced pad all operations are normal at this time.
Check out apartment for all radiators are heating But some of the vent dampers were close down not allowing to heat to full capacity Open up all dampeners check water pressure in boiler and temperature setting all operations are OK at this time