Tyler did a great job!
Replaced the bad control board Insured the furnace is working properly before leaving
Checked the geo system Found the system low on Freon again Found oil on the air coil Checked the solder fittings from the last replacement No leaks there, leak detector was going off above that fitting along the capillaries May need to return to do a pressure test Office to get with the manufacture
Checked the furnace Found the control board failed Not bringing on the blower motor Bypassed the board to allow heat Office to quote The furnace is currently working with the fan running all the time Thermostat is also not bringing on the system at the correct temperature, owner is gonna replace the thermostat
Replaced the venter fan, motor was seized, would cause the pressure switch issue Also found the port on the collector box broken that went to a pressure switch Sealed the broken side and moved the hose to the other side of the collector box Owner to replace the filter Insured the furnace is working properly before leaving
Gas valve was not the issue Found the pressure switch bad, The pressure switch shuts down the gas valve if it fails Replaced the pressure switch and insured the furnace is working properly before leaving
Found pressure witch was stuck open. Found draft fan is failing. Recommend replacing draft fan and pressure switch System is currently working. Aaron will add pressure switch cost to estimate for customer.
Need to return to dig up and possibly cut concrete slab. Customer said that Monday, Thursday or Friday next week is best for him. Need to let customer know when we will be returning.
Found cast line from sink to be rusted out. Quoted customer to replace line and also do a cleaning with either jetted or medium machine. Customer accepted and we will need 15 ft of 2 inch with (2) 2 inch ferncos.
Installed new blower motor, flame sensor and burners verified operation of furnace and that everything was operating correctly
Installed new sewage pump verified operation
Leak is in crawlspace but there is no way to get to crawlspace informed customer she would have to have a contractor come out and put a crawlspace entrance in
Replace Flammable Vapor Sensor
Found the flammable sensor tripped Needs to be replaced Office to quote
Installed 2 new washer hose bibs and verified everything was operating properly.
Performed the ac tuneup Found the system a little low on Freon, R22 system, we no longer have R22 Made the owner aware Would highly recommend replacing due to age and condition Insured the system is working before leaving Owner renewed the gold plan Gave owner estimates