These guys did a great job! They worked hard and worked good together! They were very nice and courteous. We very happy!!
Excellent work practices very detailed workmanship knowledgeable in every phase of installation. Excellent review and operation of unit at end of installation.
Couldn’t ask for better people to work with. I had trouble getting financing and they went above and beyond for me to earn my business!
Fast, efficient and friendly!
Very thorough service
These folks know their stuff! I am very satisfied with their workmanship.
Michael was knowledgeable about the services offered that we were interested in. He explained the procedures and costs of the different options.
Time to replace 29 year old heat pump system with ducting damages & restore comfort in home including duct cleaning and dryer vent renovation.
Removed boiler from residence causing CO poisoning that heated 4 radiant in-floor loops, 2 in-duct water coils, and a domestic hot water storage tank. Replaced with an outdoor NAVIEN on-demand domestic water heater, installed a hydronic water heat exchanger to boiler home heating loop, and installed all required piping and controls to heat the home, as well as the hot water, for all needs. This was a very detailed job and the results are outstanding!
Removed old HVAC equipment and installed a new YORK high efficiency gas furnace and cooling unit. Metal duct was properly sized and in great shape, but insulation had deteriorated, so we mastic air sealed all duct, installed new duct insulation, and foam encapsulated supply boots at registers and supply plenum. Enlarged return air ducting for improved flow. Replaced Freon lineset, all new drain lines with safety device for equipment, new stat, and two maintenance visits in future at no charge.
Maintenance on York heat pump
Maintenance on York furnace
Maintenance on York heat pump split system
Maintenance on a York dual fuel system/IQ Air filter change
Tune up on York furnace
Thermal Zone heat pump system frozen coil, no airflow. Poor installation did not allow overflow to be caught and soaked ceiling, leaking through. Substandard workmanship and past repairs have left a mess.
Completed maintenance inspection
New heat pump system. Gold duct Renovation with spray foam
A/C change out with 60k btu gas furnace.
Shorted electrical service on customer wiring. Old and deteriorated wire insulation shorting out power supply from Georgia Power. Electrical service rebuild is required.
Repair of incorrect wiring causing breakers to trip along with electrical damages from unstable power supply
Estimate to Install new power supply for RV electrical plug in