I just needed a light switch changed out. The tech, Phil, was nice, professional, but his visit was about 5 minutes and $175!!
Always a pleasure having Jason at my home for work needed ...
Jason arrived at my home promptly with red booties at my doorstep. Had issue with A/C he advised me of the issue quoted me a price UP FRONT and completed the job in a timely matter AND CLEANED IT ALL UP! Will definitely recommend and use again!
Nick was very professional and knowledgeable.
I paided for the replacement of a pool light transformer. Nick did a great job and cared enough to not just replace the transformer he replaced the rotted conduit that lead to it and attached it to the wall the correct way, better then it was before. Also he used a new wall bracket. I know no one else would have cared enough to resplice the old worn wires in ground box and put on new caps. He cleaned out all the small dirt particals inside the ground box and did a lot of small details that are always ignored by other people I've used in the past. Thank you Nick and King Electric.
This is the 2nd time Jason has been to my home for services and he’s always professional and clean
Inspection report: double tapping because no space in indoor panel Solution: Replace (1) 150 amps main lug indoor panel Supply and install (1) GFCI outlet and bubble cover Extend drain pipe off the exterior wall about 1 ft Permit fee will be passed through customer if requested
KITCHEN REMODEL AS PER PLANS
1)â€”â€”Remove 3 (Tankless water heater)40 amp 240 volt circuits from existing indoor circuit panel and relocate all circuits into new indoor circuit panel. 2)â€”â€”Remove 2 (Pool heater)50 amp 240 volt circuits from existing indoor circuit panel and relocate all circuits into new indoor circuit panel.
1)â€”â€”Install #4 gauge copper equipment bonding wire from pool fence back to pool equipment.
Replace (1) run dual capacitor for Condenser
Replace (1) dimmer switch
1)â€”â€”Install customer supplied dimmer in kitchen.
1)â€”â€”Extend circuit in garage from existing switch box using wire mold to desired location of outlet close to water heater. 2)â€”â€”Install wire mold junction box with outlet and cover plate close to water heater. 3)â€”â€”Remove 3 outdoor outlets and cover plates. 4)â€”â€”Install 3 new weather resistant outlets and bubble covers at all locations. 5)â€”â€”Caulk at each location to ensure weather proofing.
Replace (1) blower motor under warranty
1)â€”â€”Went through affected circuits and found incorrect voltage at all points. 2)â€”â€”Checked panel and found several loose connections including a burnt neutral from being loose. 3)â€”â€”Tightened all loose connections and repaired loose neutral.
Diagnosis main breaker getting too hot and tripped Found: overloaded main breaker because total loads is approximately 320 amps while main service is capable of 200 amps. Recommend: relocate pool heater circuits ( two 50 amps circuits) by adding outdoor 100 amps sub-panel
1)â€”â€”Remove and replace 100 amp main breaker. NOTE: Customer is aware that this may or may not fix half power related issue. FPL will be the next step for repair if issues continue.
Repairs according to the inspection report: 1. Repipe electrical pipes at the corridor next to the pool, pool equipment room and underneath the stair. Approximately 40ft on the wall and 30 ft underground. 2. Remove (2) empty junction boxes and conduit in pool equipment room 4. Install (5) screws of main panel cover in meter room 5. Install (1) cover for timer in meter room 8. Identify and label all condenser disconnect boxes 9. Replace (5) broken low voltage conduits of AC condenser units Permit fee will be passed through customer if needed Note: Work in pool equipment needs to hold until the roof done. We warranty all work done base on inspection report.
Supply and install new Rheem 3.0 ton AC Split system Supply and install hurricane tie down straps on outside unit Supply and install (1) new smart thermostat 10 year manufacturer's warranty on unit 1 year AC maintenance program on unit 1 year labor warranty on unit *NOTE* Only rheem unit will fit in existing location of air handler in closet. Existing unit is 17.5 in wide. Same as rheem