He was SUPER Wonderful Awesome 👍😃
Great service, kept in touch so I knew when the service person was coming and completed repairs within a few hours of my call.
Kings never lets me down! They show up on time, they are thorough and great at troubleshooting. I e referred them to family, friends and customers .
Would recomment tonfreinds sbd family!
Phil is good
I recommend your company and Nick, to my family and friends.
Install new 20A outlet in kitchen
SHMP123D128E-2 Approved by Lapino - Extend circuit from existing indoor outlet in living room, approximately 40ft underground - Supply and install (1) photocell - Clean the area, customer is responsible for putting sod over the area
Replace (1) used 30A 2 pole breaker Total amount will be deducted toward new panel and AC replacement Replace (1) float switch
Replace (1) regular outlet Inspect fan switches and wiring inside fan box
Replace Circuit board / Xfermer. Parts under warranty.
We were dispatched for the following Had flooding down C, D, E, Y, and H aisles, little in B aisle last week. had roofing company here but they say no roof leaks. DM requesting maintenance on ac in the main building. Also, have a small leak on 2nd floor of 2nd building in front of unit A238. The following was found : Make : Trane Model : 4TEC3F42C1000AA Serial : 93554542V Delta -18 Solution : Replaced Run Capacitor 45+5 Installed Hard Start kit. Make : Carrier Model : 24ABC636A300 Serial : 0513E06859 Delta - 20 Solution : Replaced Run Cap 45+5 Make : Carrier Model : 24ABC636A00 Serial : 0513E06901 Delta - 20 Solution : Replace Run Cap 45+5 and Replaced Thermostat. Tech Notes : When I arrived I noticed multiple units not working as mentioned above. All 3 AC's had bad run cap's and one unit had a bad thermostat as well. Also put a hard start kit on one compressor. All 3 units now are working properly.
Diagnosis hot water heater not working Replace (1) 2 pole 30 amps breaker Dedicate 240v lines for water heater which was bad
WO:20111300272 Problem: Blowing hot air Unit A122 or 1122 A122 or 1122 Brand :Carrier Model : FV4CNF005 Serial : 2817F19172 Type : Air Handler Brand : Carrier Model : 24ACC648BA300 Serial : 0218E15806 Type : Condenser Tech Notes : Upon arrival located filter that got clogged into coil. Unit short cycled also Added 2 lbs of 410A. Solution : Found clogged filter at Air Handler Coil and removed and replaced.
Upon arrival P.S Employee directed me to correct areas building C where slight smell in trunk line due to water damage . After verifying which systems go where noticed two systems that had bad delta T . System A Coil in bad shape filters have not been changed over two years. Corre
Hello Meghan! Thank you for having us stop by today to check on your your commercial signs! Upon review we concluded that the LED driver that powers your Led lights in the sign is receiver proper power. That being said, the issue with your lights not turning on has to lie in the led drivers the sign company installed. We left the power manually on so that the Sign installers can trouble shoot their issues. Please let us know if there are any further issues with the timer. It was a pleasure servicing you, Your service Electrician Jeahn C Bermudez
Run new conduit and wire for AC Disconnect on roof from 2nd floor existing electrical panel to roof. Access must be given from 3rd and 4th floor apartments in order to run conduit through. Roof Penetration must be patched by condo association roofer. Patching and painting (If needed) to be done by others. Permit fee's included.
(1) year red carpet club, 2 visits a year Perform 1st visit
Replace (1) Trane TZON1050AC52ZAA thermostat
Clean condenser coil Relocate dryer vent away from condenser unit