Approved PHM 0769010 3,000.00 Remove existing compromised aluminum underground feeder wires between the electrical meter room and the unit panel. Supply and install new copper feeder wire from the meter room to the existing electrical panel in the unit. Replace the 100-amp main circuit breaker in the meter room with a new 100-amp circuit breaker. Test and confirm the correct voltage is at the unit electrical panel.
Upgrade existing fire hazardous panel to a new and SAFE brand. Breakers are already starting to trip and overheat, highly recommended to get this job done ASAP. **Disclaimer** Any openings we have to do to get panel off and on the drywall we are not responsible for a finished surface. Repairing drywall is owners responsibility. We will do are best to leave holes covered but the texture will not be "finished"
Diagnosis 6 GFCI outlet not working Replace (4) GFCI outlets
Diagnosis GFCIs outlets not working: breaker tripped because water got into extension cord without protection Reset Breaker Install (1) blank spacer at indoor panel for safety Check power to garage door opener â€”> it has power.
Hey Edward! Thank you for calling kings electric & a/c for your electrical repairs. Today when I got to your home, you guided me to the side of your house where your electrical issues are occurring. You explained to me what the line controls and where it runs to. I was able to understand the grasp of work that needs to be done in replacing the EMT pipe with a new 3/4â€ PVC pipe and refeed the wire to pool equipment. I gave you an option how that can be done and how a surge protector will protect all equipment in that main disconnect panel. If you have any questions or concerns, please reach out. I hope you and your wife have a great Day! Your electrical technician, Xavier
Hey andres! Thank you for choosing Kings electric & a/c for your electrical upgrades. Today when I came to your home you explained to me that youâ€™ll like to add a 50 amp interlock system for your generator. After looking at everything, I explained to you the only way that can be done is if we replace the existing 200 amp main disconnect and add a new one with breaker space. I gave you (3) different options how we can get this all done for you. If you have any questions or concerns, please reach out. Have a great week! Your electrical technician, Xavier
The job was not electrical related, the issue was the refrigerator was not cooling. The customer needed a appliance technician.