I am having trouble understanding how changing a 50 amp breaker to a 30 amp breaker and installing a interlock switch can bs 895 dollars.I could understand that charge if a transfer switch was being installed, but the switch was already there. Perhaps tech made a billing error.
Technician was professional, good natured in demeanor, he explained everything he was doing and listened to what I had to say!
Kings Electric was called on a Saturday after a small electrical fire. They were really professional and accomodating. Even after the job was performed, we received a call to check on the service they had provided. I would use them again, and I highly recommend them!
Diagnosis level 2 â€” Water heater breaker keeps tripping. Found bad heat elements causing the problem. Recommend replace the water heater because itâ€™s leaking at the bottom â€” Replace (1) burnt out outlet at front door
Customer had 30A generator power inlet box installed incorrectly. Need to replace 50 amp breaker by 30 amp breaker to match with the wiring capability Also need to install interlock kit for safety and up to code
Happy Thursday Sherry Today we switched out a sconce in the front of your house! Wires were spliced messy and hanging bracket and screws were corroded. We changed the bracket and replaced the Box screws to make sure they last longer and wonâ€™t snap off. Wire were tapped or properly assuring no shortages due to bad splicing. Thank you for having us! Your Service Electrician Jeahn!
One light is bad
Perform 1st AC visit Reseal return plenum under warranty
1)â€”â€”Convert 3 defective hi bay metal halide fixtures to line voltage for LED bulbs to be installed. 2)â€”â€”Supply and install 3 600 watt equivalent LED corn cob bulbs.
1)â€”â€”Convert 5 defective hi bay metal halide fixtures to line voltage for LED bulbs to be installed. 2)â€”â€”Supply and install 5 600 watt equivalent LED corn cob bulbs. NOTE; We will need a lift, additional charges will apply.
Fix low voltage wires loose at transformer
AC not cooling
1)â€”â€”Remove indoor 100 amp FEDERAL PACIFIC main lug circuit panel. 2)â€”â€”Install new indoor 100 amp GE main lug 16 circuit panel and flip to other side of wall. 3)â€”â€”Label panel and clean area. NOTE; PATCH DONE BY OTHERS
1)â€”â€”Remove indoor 200 amp main lug CHALLENGER brand circuit panel. 2)â€”â€”Install new indoor 200 amp main lug GE brand 42 circuit panel. 3)â€”â€”Install whole home surge protector. 4)â€”â€”Label, rough patch and clean.
1)â€”â€”Remove existing ceiling fan. 2)â€”â€”Extend ceiling fan switch line approximately 5 ft to desired location and install fan rated junction box. 3)â€”â€”Assemble and install customer supplied ceiling fan. 4)â€”â€”Run switch line from existing switch box to 8 locations for new LED lighting to be installed. 5)â€”â€”Supply and install 8 6 inch round LED remodel cut in fixtures. 6)â€”â€”Supply and install LED rated dimmer. 7)â€”â€”Supply and install double switch.
1)â€”â€”Remove indoor 125 amp main lug circuit panel. 2)â€”â€”Install new 125 amp 20/40 circuit main lug panel. 3)â€”â€”Label, rough patch and clean. 4)â€”â€”Troubleshoot and repair master bed and bath/den circuit.
1)â€”â€”Extend circuit from existing outlet to cash register outlets. 2)â€”â€”Install extension ring and connect circuit to cash register outlets. 3)â€”â€”Install new outlet at cooler.
1)â€”â€”Remove indoor 200 amp main lug CHALLENGER circuit panel. 2)â€”â€”Install new indoor 200 amp main lug GE 20/40 circuit panel. 3)â€”â€”Label, rough patch and clean area. 4)â€”â€”Install surge protector at outdoor main breaker panel.