Hey Ken! Thank you for calling Kings electric & a/c for your electrical repairs. Today we came out because youâ€™re having issues with your a/c & water heater. We were able to bring power back to the unit, but itâ€™s a temporary solution. Iâ€™ve given you a price and the scope of the work. Please find out with your HOA if you need a permit or not and let us know. We hope you have a great Day! Your electrical technicians, Jeahn & Xavier
Management taken care of.
Warranty bad breaker for water heater
Replace (1) 125 amps main lug indoor panel Hardwire hot water heater Dedicate 240v 30 amps circuit by greenfield to replace existing Romex wire. Approximately 6ft Rough patch and clean area Pull permit and get inspection Note: customer is responsible for removing tile on the wall which the panel is installed before the work begins Replace (1) 2 ton AC pancake system with new high efficiency system. 10 years warranty from manufacturer and one year warranty from Kings Need crane to bring condenser up to the roof and remove the old equipment Pull permit and get inspection
Supply and install new 3.5 ton Rheem Package unit Supply and install new tie down straps on Slab Supply and install new non programmable thermostat 10 year manufacturers warranty with Rheem 1 year Labor warranty with Kings 1 year RCC membership with Kings
Diagnosis level 1 lights flickering Not including light bulbs, dimmer switches defective or not compatible
Clean (1) dryer vent with duct cleaning machine
Supply and install new Outdoor Meter Can per FPL Submit and Pull permit as required by both FPL and the city. Reconstruct/Replace outdoor concrete post.
Troubleshoot kitchen circuit to find out why microwave, GFIs and over sink light is not working. Outlet in living room behind couch was not making a good connection. We replaced outlet and fixed problem.
Repair incorrect wiring inside the indoor panel Supply and install ground bar in inside panel Install new grounding system for outdoor panel Replace 200 outdoor main breaker panel
Dryer not working Remove double tap breaker Install new 2 pole 20 amps skinny breaker Relocate few breakers to make room for new dryer breaker
Supply and install new mini split system (2) ton 12k btu Install new circuit for mini split system on new outdoor panel with new breaker
Supply and install (7) smoke detectors Interconnect each smoke to each other Tap into circuit from attic to bring power Pull permit
Supply and install new (5) smoke detectors Interconnect to each other Tap off circuit in attic to feed first smoke detector Pull permit
REPLACE 3 RECEPTACLES- 1) Remove and replace 3 receptacles. DEDICATED CIRCUITS- 1) Run dedicated 20 amp circuit from panel to 1st hair station. (Approximately 40 ft) 2) Install metal junction box and 20 amp receptacle. 3) Run dedicated 20 amp circuit from panel to coffee station. (Approximately 40 ft) 4) Install metal junction box and 20 amp receptacle. REPLACE PANEL- 1) Remove exisitng 100 amp surface mounted indoor main breaker circuit panel. 2) Install new 125 amp 20/40 circuit main breaker panel. 3) Label panel and make sure all circuits have correct voltage. LIGHTING- 1) Remove and replace 4 bulb 4 ft flourescent ballast.