EXCELLENT, he is a great value to your company
Efficiency and professional well worth the price
Kept me in the loop, they were prompt professional and tidy. What more can be said! Great Job!
Got the job done quickly. Very polite. Didn’t try to sell me things I didn’t need or want.
Nick is great! He is efficient, patient and easy to work with! Very happy I found them!!
Nick took care of all my issues, he explained the process and the options right up front, great job and my issue was fixed in no time. The folks on the phone are super friendly, great electricians to work with.
Replace (1) 150 amps main lug indoor Challenger panel by GE panel Replace (1) 150 amps main breaker outdoor Challenger panel by GE Permit fee will be passed through customer if requested
Diagnosis lights in kitchen not working Found: bad dimmer switch Solution: replace (1) dimmer switch with 1 year warranty
1 year Rcc club for AC
1)â€”â€”Extend switch line using wire mold conduit and fan rated junction from existing switched outlet to desired location of fan at 3 locations. (Living room, Bedroom 1 and 2) 2)â€”â€”Assemble and install 3 customer supplied fans.
Install customer supplied chandelier (18 ft) Replace (4) Hi Hats with LED bulbs (customer supplied) Install customer supplied outdoor fan Raise fan in kitchen 6 inches with new Gold rod Install customer fan in 2nd floor bedroom
Supply and install new indoor 150amp electrical panel.
Supply and install new copper lines from new outdoor condenser to edge of building slab. The existing copper lines have leak somewhere underground or inside the building between the air handler unit in the unit and the outside condensing unit. Original contract includes replacing the existing equipment to the EXISTING copper lines, electrical and condensate drain systems.
Perform 2nd visit Recommend UV light kit to improve air quality and prevent mold growth in the air handler
Install (1) round fixture customer supplied
1)â€”â€”Remove indoor 200 amp main lug circuit panel. 2)â€”â€”Install new indoor 200 amp 20/40 circuit main lug panel. 3)â€”â€”Label, rough patch and clean area.
AC leaking Perform 2nd Rcc visit
Remove and discard existing indoor panel Supply and install (1) 200 amps 20/40 circuits indoor panel Replace aluminum feeders from outdoor panel to indoor panel by copper and replace PVC pipe to 2â€ diameter also. *** Remove and discard existing outdoor panel Supply and install (1) 200 amps 8/16 branch circuit main breaker Re-run all pool equipment electrical into new panel including pool pump, pool light, hot tub. Also supply and install (2) 50 amps breaker for heat pump and hot tub for future installation Upgrade grounding system up-to-code Permit fee will be passed through customer if needed
1)â€”â€”Remove 150 amp FEDERAL PACIFIC main breaker circuit panel. 2)â€”â€”Install new 150 amp GE 8/16 circuit main breaker panel. 3)â€”â€”Supply and Install 60 amp fused AC disconnect.
Tech Found that pump was bad
1 year AC maintenance red carpet club. 3 visits/year Performed 1st visit