I have used Kings Electrical for several years, including major electrical panel change outs, as well as alarm system installation, ceiling fan installation, etc. Kings are prompt, tidy and the work is exemplary. I will call them for any other electrical work that I require.
King’s Electric gave us too rate service. Nick got everything we needed completed and the work is excellent. Nice to have a company that takes pride in what they do.
Great company and I would use them again and reccomend them to anyone else.
WO 201113-00272 Problem: AC unit C-1 is not cooling. Temperature reads 86 ( please check all units in C building for proper operations) Make : Carrier Model : FA4CNC048 Serial : 0307A87748 Type : Air Handler Make : Carrier Model :38CKC047300 Serial : 3301E15141 Type : Condenser Tech Notes : Found outdoor unit not running . Upon further inspection found run cap with bad mfd. Replaced run cap 50mfd and added 3 lbs of 422d replacement. Unit are in bad shape but still functioning at this time. Bad filters as well 22x22 x1 . Other unit are running accordingly at this time Solution : Replaced 50mfd Capacitor and added 3 lbs of 422d replacement gas. Replaced Filter. Checked all other units. All other units are working well.
One of the compressor is low on freon. Need add 3 lbs of R22 replacement refrigerant Recommend add leak stopper due to the corrosion on copper lines to seal the leak if possible Total amount will be deducted toward new AC replacement
Replace (1) 2 ton AC split system with new high efficiency system. 10 years warranty from manufacturer and one year warranty from Kings Permit fees Included
Replace bad switch ( customer provided)
Replace (1) 35/5 mfd dual capacitor Replace (1) 24v contactor Total amount will be deducted toward new Ac replacement installed by Kings
Happy Monday Mr Bernon! I was extremely grateful to be able to help you out last minute with your lighting situation. I was able to diagnose and resolve your issue with your lighting circuit plus put in two new switches as well. Pleasure in meeting you. Your Service Electrician Jeahn Bermudez
Perform 1st rcc visit Clean out drain pan and seal with silicone No warranty for the sealant If the leaks occur again, we will credit back half of the amount toward coil replacement
Diagnosis one room doesnâ€™t get cool air, found out the damper was closed, opened plenum and opened damper AC leaking at warehouse unit, found drain pipe clogged, cleared out drain pipe but recommend fix the drain line to prevent clogged again : Cut-out and re-support (1) drain pipe to get proper water flow
Diagnosis dryer outlet not working Replace (1) 10-3 dryer outlet
Hey! Thank you for calling Kings Electric & A/C for your electrical repairs. Today I came out because youâ€™re having issues with the power for your lights and some outlets as well. After troubleshooting and opening up the outlets I saw you had burned wire and a box as well. I had to rewire from the meter to the outlet to replace the burned wire. I also replaced 2 burned out outlets you had as well. Iâ€™m glad to inform you that everything is working and has power once again. If you have any questions or concerns, please reach out. Your electrical technician, Xavier
Diagnosis one room doesnâ€™t get cool air, found out the damper was closed, opened plenum and opened damper AC leaking at warehouse unit, found drain pipe clogged, cleared out drain pipe but recommend fix the drain line to prevent clogged again
One Bay lost power Warranty previous job
Install (1) photocell customer supplied Diagnosis (1) outside not working in bay 38 Found losing breaker, fixed it
Run 100A 3P Circuit appox 25 ft from panel to machine. Supply and install 3P Breaker. Hardwire Machine. Customer will be supplying transformer with this estimate.
Check electrical wires to make sure they are dead and cap them off