As per customer, stove top unit was tripping breaker. Upon further investigation. Performed a amp probe test with max burners on full force. Amp probe shows only a max amp load of 24A. Stove is on a 40A GE full size breaker. No upgraded breakers available. In conclusion, electrical for stove is on a dedicated 40 A breaker with #6 wire and cannot be the issue with the fuse blowing. Wire from burners to control board should be checked for short or undersized wire.