500 dollars for a 60 minute job
Great service like always
Gave verbal estimate 8600.00
Heater activated on heat and CU activated on cool but in both cases blower motor failed to initiate, tested blower motor on fan on blower motor still failed to initiate. Replace blower motor.
Replace old Challenger exterior main breaker panel with new panel and breakers. Permits are not included. Patching and painting by others.
Replace thermostat with new digital, thermostat. Refrigerant needed to be added.
Disposal and dishwasher on same circuit and adding a car charger under panel
SHMPA29E82D4-1 PHM 0935312 Replace switches, dimmers and GFCI's 400 amp square d panel
Multiple outlets, lights not working Customer replaced switches and lights donâ€™t turn on. All wires has been disconnected from original wiring. Need to trace all switch legs, 3-way switches system.
Replace TXV Valve Replace Filter Drier at Unit. Replenish Freon. RCC Membership
Extend existing dryer outlet to another location, run 3/4 EMT approximately 12ft, surface mount
Replace (1) blower fan motor under warranty
Supply and install (2) electric round boxes for ceiling lights (not UL box for ceiling fan)
1 year AC red carpet club for split system
Remove existing panel Remove aluminum feeders Replace 200 amp indoor main breaker panel. 35 circuits. Run new copper feeders from meter, approximately 5ft, wire size 2/0