The customer is wanting to find out what thermostats actually control the air handler. Currently it is running cooling non-stop I was told they turned all the thermostats off I was still cooling. The control panel is downstairs on the wall I was unsure on how to adjust the controls or what sensors go to the controls panel. I was here 10:45-12:45. 6/10/20--Checked the multizone air handler and condenser for continuous run. Found the control panel in the basement with the cooling discharge temp set to 8 degrees causing continuous run. Set the control above the discharge temp and verified the shut down of the condenser. Set the control to 53 degrees for proper control of the system.