Quick response to our A/C problem, very friendly and courteous.
Was nervous about an emergency charge, but it was worth it.
This is the first time, out of many maintenance visits, a technician has checked the batteries in my thermostat! I was so impressed!
My kitchen sink is not working, it did before they came, it did not when they left! NOT HAPPY!! The work they did is satisfactory, but not the sink. Fix one thing and leave another ####ed up. Not happy, I need it fixed!!
Always have trusted LBA for our heating and cooling needs. Thanks!
Checked the North IT room Daikin mini split for no cool. Found the unit low on refrigerant. Leak searched the unit and found the leak at the condenser low side flare connection. Repaired the leak. Removed and weighted the existing R410a. Added back the removed refrigerant and added new to the correct charge. Started the system and verified operation. Also verified the operation of the South Daikin mini split for the IT room. Checked the commons entry area Daikin cassette for A3 error code of condensate drain back up. Cleaned the condensate line and the pump-float sump. Started the unit and verified operation. Repairs were approved by Karyn Forsythe
Found some worn flappers and 1 fill valve , customer said he will repair himself
Estimate to repair water line
Arrived to find unit not operating. Due to being low on refrigerant. Performed leak search on heat media transfer coil. Found a leak in the heat media transfer coil. Called customer to go over options. Customer wanted a quote on all the options and also wanted a quote on a new system. Turned system to the off position at the Thermostat. Unit is not operating within factory specifications at this time.
Checked all operations in the cooling mode. Checked all electrical components on the outdoor unit. Washed out outdoor unit. Found a restriction present. Upon further inspection txv, txv acted as it was supposed to. System was cooling at this time. Informed customer of this issue at this time and told customer to call back if issues occur.
Upon arrival found RTU covering front office low on refrigerant spoke with customer who wanted system charged at this time as they would be moving after this season added 2 pounds refrigerant to system now operating well not all time charged for as had to have refrigerant delivered.
Rebuilt 2nd floor womenâ€™s room toilet on right stall , tested flushing and adjusted , all flushing good now .
RTU#3 found not cooling. Thermostat has failed and was not sending the proper voltage to the Y-cooling terminal at the unit. Thermostat has been replaced with programmable options. Conducted a test start-up on the unit, unit is operating properly at this time.
Estimate for sump discharge and washing machine valves will do work 3:00-4:00 tomorrow
I took out old kitchen faucet and installed a new customer supplied kitchen faucet. Customer also wanted to renew his monthly P3. Everything tested good. Customer also had a $50 off coupon.
I arrived to find that the condensate pan for the indoor coil was overflowing. I presented repair options to clear the drain line and the customer chose the platinum repair option. I chemical flushed the condensation drain line, installed a secondary drain line, installed a float safety device, cleaned the blower assembly /housing, installed a drain treatment pad and replaced the air filter. After flushing the drain line with 5 gallons of hot water, the condensation drain line is draining properly at this time.
Cleaned kitchen drain from behind washer , tested flow all ok
Completed cooling tune up, performed chemical coil clean on condenser unit, everything else tested as it should at this time
No work was done.