Steve came in on a Sunday at 7 am to make a hour drive to Lawrence to service a non working wall in freezer The freezer was full of product and Steve was able to get the walk in up and running in less then an hour and then went home and researched the codes that where displayed and reached out to us to visit about what he had found He was terrific
Used them for years and never had a issue
Andrew is great. Quick, efficient, and friendly👍👍
Our A/C stopped working in the middle of the recent heat wave. We called early in the morning, and they had an opening and Eli arrived within an hour. He quickly found the problem and it was running in less than an hour. We have been totally pleased with the service from L.B.A.
Did a great job to our satisfaction!
I was told that the units froze up over the weekend during the high heat. I found the thermostat set to 67 degrees, this would cause the evaporator to be in a freezing temperature. I also discovered dirty filters by the furnaces. Both blowers were hot, I also found the black blower wire tied into line 1. Both units have a 20 degree temperature split. Super heat 18 Subcool 8 I was also informed that the units only run during service. This can cause the condensation to become unmanageable, as far as humidity and temperature go. The humidity was 62 percent indoors. I also discovered several supply registers closed and opened them.
Upon arrival customerâ€™s kitchen sink will not drain. I ran Spartan 100 full length. I ran cable five times in and out. Each time paying attention to tight area and ran multiple times through tight area each time. Each time I tested I could not get drainage. We recommend jetting line. I could not clear blockage so we did not charge for today.
Arrive to customers home Tuesday, August 3, 2021. Customer has leak near water heater in basement utility room. Found leak coming from kitchen sink drain line and ceiling of basement. Customer agreed to go through with work. Cut copper drain in ceiling of basement bathroom and re-piped to main stack with PVC. Piping was very tight in ceiling. Connected to copper drain with fern co-fitting. Upon completion of re-pipe ran kitchen sink for roughly 10 minutes to ensure piping was leak free. Company will have one year warranty on re-pipe. Thank you for choosing LBA have a wonderful Day. Attention Liz! Please bill customer.
Performed full cooling maintenance on 2 split systems. Checked mechanical and electrical components, cleaned condenser coils, checked temperature splits. Quotes have been sent for replacement parts. Units are cooling properly at this time.
Checked all operations in cooling mode. Return filter didnâ€™t need replacing at this time. Found that the system was low on refrigerant due to a leak. Spoke to the customer on options for a bandaid, repair, or replacement. Since the system is 16 years old customer wanted an estimate on replacement before doing repairs. Had a design specialist out to give options on replacement. Thanks for having me out today it was good to meet you!
Gave estimate to run new gas line to kitchen island and make range connections. Decided to have inspection performed on another day.
8-3-21. 3.5 hrs Sanctuary north 10 ton rooftop unit #5 is tripping the main circuit breaker. Unit will run in AC mode for about seven minutes then tripped the breaker. Isolated the compressor tested it for grounds and shorts weâ€™re both my multimeter and it Megger. Megger readings fluctuate between 20 megohms and 100 megohms. Spoke with Key refrigeration Brian Nelson. They had me take some reference readings pressures and temperatures. I pass them on to him Spoke to Brian they are going to order us a compressor and expansion valve and liquid line dryer. Ruud Model # RGEDZR102ACA222AA Serial # F432000042 Comp Copeland mod ZP91KCE-TF5-130
No cool found unit with busted belt, replaced (1) A-38 belt, checked supply motor amps , an operation of cooling mode everything is working ok
Company arrived on august 3rd 2021. Rental property. Customer is having sewer smells from basement floor drain. Upon inspection company found that branch line off of floor drain does not have clean out plug. Company called landlord multiple times, but did not answer. Company left voicemail explaining situation. If customer wants company to come back and install clean out plug it will be $250, or customer can do it himself. Service truck fee is due today which is $89 dollars. Company will put on billing due to fact that customer did not answer. Thank you for choosing LBA and have a wonderful day.
15+ year old lennox ac and coil 3 options to install new system. Reviewing, follow up tomorrow.
Checked all operations in the cooling mode and found that the air conditioning system was low on refrigerant and the fan motor is leaking oil. Customer was not interested in making repairs at this time. replaced furnace filter at this time.
Installed new Lineset. Performed pressure test and vacuumed down to 390 microns. Added some refrigerant tested system operation. System is cooling and operational at this time.
Thank your for allowing LBA to service your HVAC equipment today. Performed maintenance and safety inspection on the air conditioner. The filter did not need replaced at this time. Flushed the condensation drain. Washed the coils on the outdoor unit. Tested all electrical and mechanical components on the air conditioner. The refrigerant pressures are within manufacturers specifications at this time.
Customer has Seven bathrooms and all original toilets Approximately 15 to 20 years old. Customer requested to replace upstairs toilet due to leaking, and company offered bundle deal in replacing multiple toilets at discounted rate. Customer chose to replace two toilets at this time being upstairs guest toilet and master bathroom toilet. Company also gave bid to replace five remaining toilets as a bundle deal for a later date and company is going to conduct toilet replacements on master and guest upstairs bathroom today on August 3, 2021. Company Removed old toilets and wax rings cleaned the areas around and under toilets and removed old supply line and emergency stops.Company put new double wax rings for maximum sealing and connections between toilet bowl and flange. Installed the new braided supply lines and new emergency quarter turn stops. Company also reinstalled bidet aftermarket toilet seat connection to new toilet in the master bathroom and Blew out all air from water lines the
Upon arrival urinal in main floor menâ€™s restrooms was holding water. Cleared trap but had to remove urinal from wall to auger line. It took multiple tries to clear line. Ran line 10â€™ with line clearing in the first 3â€™. Flushed with water and cleaned workspace.