Tom was very helpful explaining what he thought the issue was with our bathroom and scheduled a follow up appointment with a LBA plumber.
Michael was courteous and professional.
Great service. Very pleasant technician
Nathaniel identified the drain problem right away and gave us a thorough explanation of available options. We selected the Bronze package and are very pleased with the service he provided and results. We’re most appreciative of his constant awareness of social distancing and professionalism with a cordial smile!
Chris did a wonderful job with Doug fixing the mess the first guys did
We are very pleased with your prompt and professional service. You quickly assessed our problem in our shower and provided the right solution.
Upon arrival customer took me to the basement where the washer box was leaking. I showed customer options for repair. She chose the bandaid repair. And had me check natural gas piping and there was a leak on the old gas caulk to the dryer. I showed customer options for repair and she chose the bandaid repair. I removed gas caulk and capped and checked for leaks. Water leak was a shark bite fitting. I repiped with pex fm adapters.
Upon arrival customer took me to the basement where the floor drain was overflowing. No cleanout available . Cut in cleanout in stack. And ran large machine. Ran three times pulling back roots each time. Got to drain and ran water no backup.
Quoted work for combo pump. Installed 2400 series combo pump. $2198.00
On arrival unit was operating within factory specifications. Checked filters pressures temperatures and flame rectification sensor and was unable to find an issue at this time.Formed customer to leave the system on if it does fail again.
Upon arrival found that the pressure control system had failed will return Monday morning to perform a pressure control system repair as well as washout both air conditioners and change furnace filterâ€™s.
Checked all operations in the cooling mode. Washed out the outdoor unit which was extremely dirty. Replaced furnace filter. Found system to be leaking at the heat media transfer coil and to have a bad metering device. Added refrigerant at this time. Customer is going to give us a call back upon replacement of the heat media transfer coil Which will also include replacement of the metering device.
Customer broke handle and cartridge for Moen kitchen faucet. Customer chose bronze faucet replacement. Replaced original faucet with delta Leland kitchen faucet, also replaced original stops with quarter turn Straight stops. Installation is working and testing OK at this time thank you for choosing LBA and have a wonderful day!
Upon arrival the customer was smelling gas in the house. Customer said that they been smelling the gas ever since they moved in and the gas company turned it off today. Customer wanted a gas test done so we are rescheduling to come out Saturday 28th. Quoted the customer on just the gas test at $450 plus charges on repairs. I will collect the trip charge today and credit that back to repairs only on Saturday.
Arrived on site for lack of cooling. Checked in with Rodger. Replace customer supplied air filters in 7 Ahu's on the west side of building. Found unit #28 not cooling as much as it should. Temperature split was 10*. Access unit on the roof and found compressor overheated. Cooled compressor down with water. Discovered low ambient switch not passing power to condenser fan. The high side pressure was 450 # and the switch is set close at 365#. I also notice oil around low ambient switch. Sprayed switch with soap bubbles found switch leaky. Removed switch form service and top off refrigerant charge. The switch will need to e replaced for low ambient cooling.
Checked all operations in the cooling mode. Furnace filter is OK at this time. Washed out the outdoor unit. Checked all electrical and refrigeration components for the outside air conditioner. System is operating un level at this time.
Conducted CPMA on the 2 remaining split systems. Inspected all electrical and mechanical cooling operations. Inspected all motors and capacitors electrical tolerances. Inspected condition of the blower wheel, and belts. Cleaned all outdoor coils, and replaced all filters. Checked for correct cooling temperatures. The package unit for the paint booth filters and coils have been cleaned. A full check out sheet will need to be completed by a senior technician.
Performed a full heating inspection. Checked all wires and safety switches. Cleaned indoor unit. Unit is operating within factory specifications at this time.
Customers main line was back up again and this time we had to pull the toilet to cable the line. When cabling we discovered that there is a clay clean out right next to the walk way to the front door. When getting the clog out we also ran gallons water. I also had to replace the shut off to the toilet. Everything tested good.
Helped Nate on main line clog. Had him pull toilet to run proper size machine in clogged main. Small machine will not clean a main. While pulling toilet I found original clay clean out in front of house. Line is fully open and draining at this time
After removing floor for access, jackhammered out concrete floor under addition in the back of house. Installed new 4â€ c/o for access to cleaning main line to street,cabled multiple times from c/o to remove roots. Also pressure cleaned for sludge build up. Line is open and flowing at this time. Customer will be placed on a preventative maintenance per Pat for $205.00 to cable line and inspect if needed.