Jeremy was very professional and did an exceptional job for us. Will recommend him to others needing similar service.
Fair Price, Did what they said needed to be done without an Upsell.
Nate was courteous and friendly. Every thing is working now. He had to come back due to Water One issue, and did this with no complaints,
Nathaniel got the work done and explained to me what he had done, and he also suggested something else that could help my situation.
Did a fine job, took extra care to protect against leaks, great to work with Nate.
Very happy with installation of furnace and air conditioning. All personnel were very easy to talk to and very professional. I would recommend them to anyone who needs help.
Customer had clogged floor drain after further investigation company found that floor drain trap was completely crushed company gave estimate to do 2 foot repair replacing floor drain itself while conducting repair company informed customer that 2 inch line for Floor drain was cracked and breaking apart not allowing company to tie on. Company reconfigured bid to 3,000 to chase broken line to tie on to a good piece of pipe. Company cut out approximately 12 to 13 feet of line tying onto solid piece of cast-iron. Company also conducted to other tasks for no charge of trying to cable secondary drain located another room which company was unsuccessful customers line for that drain is broken approximately 12 to 15 feet in. Company Will send estimate if customer wishes. Company also installed 4 inch fern co-cap around broken pipe on main stack itself. All installations done by LBA are working and testing properly at this time thank you for choosing lba and have a wonderful day.
Upon arrival menâ€™s break room urinals and one of the menâ€™s office urinals were slow or backing up. Ran urinal auger through all urinals. All are flushing and draining. It is recommended that the be acid treated by LBA at a time the urinals will see little to no use. This will help to decrease the build up inside the fixtures.
Performed maintenance and safety inspection on the furnace. Customer asked if humidifier was operating properly. Tested humidifier and it is working without issues. Indoor humidity read at the thermostat was 40% and the humidifier was set on 35% humidity. Humidity was adequate in home. Performed a combustion analysis on the heat exchanger and found zero issues. Inspected all electrical connections to ensure they are secure and not rubbing. Customer is waiting for his filters to arrive. The current filter is still okay for a few more weeks. Furnace is running safely and within manufacturers specifications.
11/24/2020 Customer complaint that boiler is not heating, trouble shoot operation and found that circulating pump breaker had tripped, try to reset voltage to pump for a start up but pump trips Immediately, motor for the pump is bad and the whole pump assembly is require to be replaced Spend all day trying to locate a pump assembly but didnâ€™t have any luck the earliest I come have got one was 1/18/2021 Zack called back today at 3:51 pm saying that originally another company had already had a bid on replacing the pump and had the part on the shelf, he was going to have them install the pump
Performed full heating preventative maintenance on two splits, checked all electrical and mechanical components, changed all filters.
Arrived at home Tuesday, November 24. Customers floor drain in basement blocking up with sewage. Customers basement toilet also bubbling when upstairs toilet was flushed. Snaked through cleanout in basement. Snaked roughly 30 feet and cleared drain. When pulling up snake found wet wipes and hair on cable. Ran water in bar sink downstairs and also in bathroom lavatory and flush toilet multiple times to ensure drain was completely clear. Had customer flush toilet upstairs while technician was in basement bathroom. No bubbling occurred in basement toilet after drain was cleared. Drain clearing today will have no warranty. Thank you for choosing LBA have a wonderful day.
Welcome to LBA Performed maintenance and safety inspection on the furnace. Customer had a concern about water around base of furnace. Found gasket to the combustion box had failed. Quoted repair and customer accepted. Picked up OEM gasket from Goodman and proceeded with repair. Test unit for 15 minutes and checked for leaks. No leaks present at this time. Performed a combustion analysis on the heat exchanger and found zero issues. Humidifier is on and had a minor leak which I fixed. Enrolled customer into our P3 Maintenance Agreement. One plumbing and AC visit still owed to customer. Furnace is running safely and within manufacturers specifications.
Arrived to residence to find that the furnace had kicked off on high limit, due to all upstairs zoning dampers closing at the same time and only allowing air to travel to the downstairs room addition. We adjusted the by-pass dampers to allow some to escape to the upstairs rooms. We let the unit run for 1.5 hours. Room addition rose up to temperature. And upper level maintained set temperature at 65 degrees. System is working within manufacturers specs. Heat temp rise upon departure was 52 degrees, this is after we made adjustments to dampers.
Upon arrival I found break room sink not draining and leaking under cabinet, when removing P-trap from wall, galvanized piping broke off flush with block wall. Made customer aware that we would return on Tuesday with second man and remove cabinet and break open block wall, replacing existing piping with PVC. Re-installing sink and to test for operations, also noted that shut offs on cold side do not work and will need replaced. Quoted 2 men time and material. 11/24 Upon arrival Mika and I remove garbage disposal disconnected piping open the wall removed existing double sanitary tee. Ran sewer machine. Install sanitary tee.Connected piping. Ran water to make sure blockage was clear.
Performed maintenance and safety inspection for the boiler system. I found out the system is operating properly and safely within factory specifications. I also conducted a gas leak search on all of the exposed gas lines. I did not find any gas leaks at this time. Boiler is currently operating within manufacture specifications.
We will cut out and remove cracked 4â€ cast iron wye along with itsâ€™ connection fittings. We will replace wye and fittings and test for leaks. Performed quoted work. Inspected for leaks
Inspected unit #1 ,#2 and #3 for crack heat exchanger York 1 model# ZF072N10N2AAA1 Serial # N1N1484702 found two large cracks along the seams of the heat exchanger and need to have it replace , the unit is 9 years old York 2 Model# ZF072N10A2AAA1 Serial# N1L2234769 found a small 1/4 inch hole in the heat exchanger an need to be replace , the unit is 8 years old York 5 Model# DM090N15N2AAA4A Serial# N0G6724641 found multiple 3/8 inch hole in the heat exchanger an it need to b replace, the unit is 12 years old Heat exchanger for both units #1 and #2 are on back order per York supply, not available for ship unit first week of January 2021 , unit#5 heat exchanger is currently average as of 11/24/2020
Performed furnace maintenance. Checked humidifier operation and recommended humidifier tuneup. Customer approved humidifier tuneup. Humidifier is operational at this time. Checked all components of the furnace. Performed a visual safety inspection of the heat exchanger. I found no breaches or cracks in the heat exchanger at this time, I did find signs of heat stress in the heat exchanger. Recommend installing carbon monoxide detectors on all levels at home. Completed a combustion analysis. Completed all other checks and cleanings. System is heating and operational at this time.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, found microbial growth in system and recommended having the I wave r installed. everything tested as it should at this time, thanks for choosing Lba, Eli
Upon arrival I found that the pressure sensing system was failed closed. After speaking with the customer customer decided to go with repairs. Repaired pressure sensing system and tested all operations. Furnace is operating within factory specifications at this time.