Izzy was knowledgeable, professional, and courteous. He did did a great job and also explained his recommendations and rationale very well!
Technician was good. But only took about an hour to clean the burner. $700.00 I can almost buy a new furnace.
Izzy was prompt, very courteous and took care of my furnace problem right away. I will definitely call LBA again for my Plumbing and HVAC needs.
justin was very pleasant and professional. he was able to get here earlier than expected which worked out great for me. he was also very honest which i appreciated .
The service man was very nice.
I replaced the blower motor under warranty from a platinum repair that was completed on 11-18-19 job#34555481. After completing the repair, the FA4CNF024 Carrier electric heat air handler and heat pump were operating within the manufacturers tolerances. The customer is meeting with Scott on 1-18-20 to go over new equipment options and LBA has issued a partial credit of the original repair completed on 11-18-19 to go towards new equipment if the customer chooses to do so. The credit issued is only good for 30 days in the amount of $1,509.00. Thank you
Upon arrival found that there was an intermittent safety system failure after speaking with the customer customer was morning interested in the replacement of the whole furnace itself due to its age. Temporarily repaired the safety system on the furnace and cleaned all safety sensors. Tested all operations the system is operating at this time. We scheduled appointment with the system design specialist to go over replacement options.
Upon arrival the customers laundry shut off was leaking. I had to cut out the wall and replace both shut offs with new ones with pex to poly fittings. I turn he after back on and tested for leaks everything tested good.
I found the rollout switch to new open on the RTU at the far south side of the building serial #5698C00829 I closed the switch and the unit heated just fine. I also noticed the blower belt was stretched and cracked so I replaced it. The unit is heating as designed at this time.
Upon arrival commode was slow filling due to buildup in lines. Replace short portion of water line and installed new stop.
Upon arrival found that the condensate pumping system had failed. After speaking with the customer customer chose bronze repair allowing me to replace the entire condensate pump system. Tested all operations after repair of the pumping system system is now operating within factory specifications. Customer signed up for 1 year agreement.
Complete a furnace tuneup and safety inspection on furnace. All safety switches are working to their specification. Perform the indoor blower test, indoor blower motor is working within guidelines. Recommend cleaning blower motor. performed an electrical test, high-voltage and low-voltage communicating properly within furnace. combustion motor is recommended to operate no higher than 1.92 A it is operating at 1.9 A. Would recommend replacing combustion motor. Due to the age of the unit Gave customer options for repairs but also recommended may be looking at options of a new system.
New 50 gallon Ruud water heater and 2 gallon expansion
Upon arrival I found the blower motor getting power to the motor but it would not turn. Blower motor has failed electrically. Jeff gave me a authorization to replace the blower motor. After installing new blower motor I test of the unit and it is operating as designed and has a temperature split that is in tolerance.
Performed a safety inspection, all safety switches are working to specification. Cleaned all safety switches in recalibrated. Performed combustion analysis, combustion motor is operating within guidelines. carbon monoxide is being pushed out of the house properly. Performed electrical test, all electrical from low-voltage wiring to high-voltage wiring communicating properly. Performed indoor blower test, indoor blower motor is working within specification.Furnace is running to specification. Would recommend cleaning blower motor. Also water heaters from 2001 would highly recommend replacing water heater. Does deteriorate on the inside, recommended lifetime 12 to 15 years
Upon arrival, the customer informed me that the Lennox G43UF furnace system was making a loud and unusual noise while operating. After further investigations, I discovered that the inducer assembly is responsible for the noise. The customer requested that I look at the blower motor as well. The VEC serving the blower motor tested outside of the manufacturers tolerance so I recommended that that component be replaced but I found the blower motor to be in good working order. The inducer is pulling 2.2 amps and the motor is rated at 2.35 amps. I tightened the motor to the inducer housing, the housing to the collector box and the collector box to the furnace attempting to resolve the noise caused by vibrations which the noise remained. Something in the inducer assembly is out of balance which is causing the abnormal vibrations in turn creating the noise. Lennox inducer assembly part number 83m56. The customer chose the gold level HM8D complete combustion exhaust renovation option but has
Performed a safety inspection, all safety switches were responding to manufacture specification. Performed combustion check, combustion motor is operating within manufacture guidelines and properly distributing carbon monoxide out of the house. Performed indoor blower test, indoor blower motor is working for specifications. Would recommend a deep cleaning on blower motor. Performed an electrical test, 120 V going to furnace secure and stable at furnace. Low-voltage wiring secure and stable from board to thermostat. Low-voltage wiring communicating properly. Furnace is working to manufacture specification.
Performed furnace tuneup, all safety switches were corresponding to specification. Completely cleaned safety switches and recalibrated. Performed an electrical test, 120 V going to furnace Secure and stable at furnace. Low-voltage wiring stable and secure from thermostat to board. Low-voltage wiring communicating properly. Performed combustion analysis, combustion motor is operating within guidelines and properly pushing carbon monoxide out of the house.Completely cleaned all cabinet space with the furnace would recommend doing a deep clean on blower motor and blower motor wheel. Could cause restrictions down the line and failures. Furnace is working to manufacture Specifications.
Per approved proposal replaced the seized inducer motor. Cycled unit and tested to assure proper operation. Unit is now working within manufactures specifications.
Upon arrival the customer water heater in the womenâ€™s bathroom in the ceiling was heavily corroded and leak. There werenâ€™t getting any hot water from it as well. I quoted them a new 30 gallon electric water heater with a complete code upgrade that will take 2 people to install. Also in the workshop there is a bathroom in the back of the building thatâ€™s not getting any hot water at all as well. The 50 gallon gas water heater is 14 years old and needs to be replaced. We can replace it with a complete code upgrade that comes with a protection pan and a expansion tank. This will be a 2 man job to install as well. Both jobs will be time and materials.