Phil was communicative and gave me many options, in a wide price range. will use again.
We had a leaking toilet and LBA was able to come out quickly and repair the problem. Phil did a great job, he found and fixed the problem and explained what he did to do the repair. We have used LBA for over 25 years and are always very satisfied with their service.
He was very good at explaining what he was doing a good young man
Great guy! Very knowledgeable
Performed a full heating inspection. Cleaned indoor unit. Checked all wires and safety switches. Performed heat exchanger inspection. Heat exchanger passed inspection. Units are operating within factory specifications at this time.
Checked the 13 ton split condenser marked ACCU-1A for no cool. Found the #1 curcuit void of refrigerant and the compressor failed due to the lack of refrigerant. Found the #2 curcuit void of refrigerant due to a cracked line at the hot gas bypass valve. Repaired the leak, evacuated the system and recharged the curcuit. Verified operation. Checked the ERV-9 for the upper level south mechanical room for noise and no energy wheel operation. Found the intake motor with the bearings failed and the existing motor for the wheel wrong over-amping the transformer. Will pick up the parts and return to make the repairs. Todays repairs were approved by Joe.
Arrived to find that the pressure port was plugged with sediment and debris. Given the condition of the furnace I presented repair options to do an extensive furnace cleaning and bring it back as close to like new conditions as possible. The customer chose the platinum option for the furnace cleaning. I completely disassemble the furnace and cleaned every component. While cleaning, I tested the voltage enhancement component for the indoor blower motor in it tested below factory specifications. I replaced the voltage enhancement component under the furnace cleaning repair option. I also performed a combustion analysis to make sure the furnace is operating properly and safely. The furnace is now operating within factory specifications. Combustion Analysis Readings O2: 8.7% CO: 30ppm Flue Temperature: 375 degrees CO2: 7.5% Efficiency: 80.5% Heat Exchanger: passed digital and visual safety test
Upon arrival furnace was not turning on. Fully diagnose system the system was missing a roof Wind cap that connects to the flue and the Combustion of the furnace. Causing the combustion to being clogged up and getting the motor stuck. Put a new wind cap on rooftop And fully restored the furnace to manufacture specification. We changed filters and cleaned and restored all safety switches. Did a tune up on 2nd floor system
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system. performed combustion analysis, checked for proper heating transfer, changed air filter, recommended using better filters and found that flue was rusting, gave customer estimates to replace and she said she would get back after she talks to spouse, everything else tested as it should at this time, thanks for choosing Lba, Eli
Replaced filters and made a list of the equipment.
Performed a full heating inspection and humidifier inspection. Checked all wires and safety switches. Performed heat exchanger inspection. Heat exchanger passed inspection. Also cleaned both units. Change humidifier pad. Both units are operating within factory specifications at this time.
Upon arrival on site technician from Henry Schein stated that person we were to meet with was out on a personal matter and that he was not available to deal with the installation of the pump in mechanical room in garage. Told him that I would note the decline for service at this time and charge for time on site.
I performed a safety and maintenance inspection on the furnace. I found the system to be operating within the manufacturers tolerances at his time. The customer purchased a humidifier tune up as well as renewed their P3 membership choosing the annual recurring option. I noticed in the notes that LBA completed a major flue rebuild last year so as a courtesy, I inspected and I found the flue to be in good working order. Thank you
Installed eemax water heater in upstairs bathroom. Ran lines from under sink next to cabinet on opposite wall. Installed new main shutoff in basement after water meter.
Performed a full heating inspection. Checked all wires and safety switches. Performed inspection on heat exchanger. Heat exchanger passed all inspections. Cleaned indoor unit. System is operating within factory specifications at this time.
Warranty visit per Pat, Installed new customer supplied pedestal sink faucet with new stops and supplies. Quoted: $100.00 for new stops.
Found Mini split in conference room not coming on due to communication fault. Check voltages, wiring connections, condenser fan motor, and control board. Reset unit and check heating and cooling operations. All test and operations are normal at this time.
Performed heating maintenance. Changed out filter. Customer declined humidifier tune up at this time. All wiring are stable (low voltage and high voltage). All safety switches cleaned and recalibrated The system is draining properly. System is running to manufactures specifications.
I performed a safety and maintenance inspection on the furnace. At this time I found the system to be operating within the manufacturers tolerances. I found that the humidifier had never been ran so I explained to the customer how to operate the equipment also how often we should maintain the equipment. Additionally, I left the humidifier operational for this fall/winter season. I also discovered gas piping that isnâ€™t to code and explained the risks to the customer however I did not find any active gas leaks at this time. The customer used a postcard mailer coupon to bring todayâ€™s service to $77. Thank you