Met Justin on site for the scope of work requested. Checked the 25 ton Carrier for a compressor failure per others. Found the #2 compressor for the #1 tandem curcuit disabled at the contactor. Megohmed the compressor windings. Found the compressor short to ground. Quoted the repairs. Sent Justin the quote via email.
Camera a main line