Checked heat pumps #6, #13 and #18 for the grade school for no cool. Found #6 off due to blown fuses to the transformer supply. Found the connector shorted to the transformer causing the fuse failure. Bypassed the connector, replaced the fuses and verified operation. Found #13 running normal after the condensate drain was cleared. Found #18 with the compressor off due to the low pressure curcuit being open. Found a wire pulled out of the low pressure switch connector. Repaired the wire and verified operation.
Rtu 21C--High school commons--replace the failed condenser fan motor--$781.42 Furnace #4 annex--repair the separated pvc flue--$147.00 Rtu 26--Grade school entry--replace the broken condensate trap--$70.88 Rtu 1--High school--replace the weak blower run capicator--$82.15 Rtu 2--High school--replace the weak condenser fan capicator--$72.91 Rtu 10--High school--replace the weak blower run capicator--$82.15 Rtu 5--High school--replace the weak blower run capicator--$78.09 Ahu 12--High school gym--replace the broken blower belt--$81.17 Prices include the factory replacement parts and labor. Total for the listed repairs = $1,395.77 3/20/2020--Made repairs as quoted. Quote was approved by Travis Laver
Quoted repairs and emailed Travis Laver for approval.
Assisted rigo with maintenance
Assisted gary with maintenance
Assisted with maintenance
Assisted with PMA
Assisted gary with cooling maintenance
Checked the York Rtu #14 for the high school for intermittent no heat complaint. Found the ignition module failing causing the burners not to light. Replaced the ignition module with a site stocked spare. Verified operation. Checked the Changeair unit #17 for the IT room for no cool. Found the unit calling for cool from the Trane EMS with the unit discharging heat. Found the reversing valve overridden to heat only in the EMS. Released the overide and found the unit cooling normal. Explained the repairs to Larry S.
Replaced the rusted out heat exchanger in the York Rtu #20 for the High school music room. Verified operation after repairs.
Checked the York Rtu #20 for the high school music room for no heat. Found the flame roll out tripped due to a failed heat exchanger. Ordered a replacement exchanger from the factory special order. Also checked the York Rtu #10 for the high school Library for no heat. Found the inducer motor seized up from a mud daubers nest. Cleaned the inducer motor and verified operation.