Rtu 21C--High school commons--replace the failed condenser fan motor--$781.42 Furnace #4 annex--repair the separated pvc flue--$147.00 Rtu 26--Grade school entry--replace the broken condensate trap--$70.88 Rtu 1--High school--replace the weak blower run capicator--$82.15 Rtu 2--High school--replace the weak condenser fan capicator--$72.91 Rtu 10--High school--replace the weak blower run capicator--$82.15 Rtu 5--High school--replace the weak blower run capicator--$78.09 Ahu 12--High school gym--replace the broken blower belt--$81.17 Prices include the factory replacement parts and labor. Total for the listed repairs = $1,395.77 3/20/2020--Made repairs as quoted. Quote was approved by Travis Laver
Quoted repairs and emailed Travis Laver for approval.
Assisted rigo with maintenance
Assisted gary with maintenance
Assisted with maintenance
Assisted with PMA
Assisted gary with cooling maintenance
Checked the York Rtu #14 for the high school for intermittent no heat complaint. Found the ignition module failing causing the burners not to light. Replaced the ignition module with a site stocked spare. Verified operation. Checked the Changeair unit #17 for the IT room for no cool. Found the unit calling for cool from the Trane EMS with the unit discharging heat. Found the reversing valve overridden to heat only in the EMS. Released the overide and found the unit cooling normal. Explained the repairs to Larry S.
Replaced the rusted out heat exchanger in the York Rtu #20 for the High school music room. Verified operation after repairs.
Checked the York Rtu #20 for the high school music room for no heat. Found the flame roll out tripped due to a failed heat exchanger. Ordered a replacement exchanger from the factory special order. Also checked the York Rtu #10 for the high school Library for no heat. Found the inducer motor seized up from a mud daubers nest. Cleaned the inducer motor and verified operation.
Checked the Changeair unit #10 for no heat. Found the wiring shorted to the 460 x 240 volt transformer and the fuses to the transformer blown. Repaired the wiring and replaced the fuses. Verified operation. Checked the Changeair unit #19 for no heat. Found the same issue as the #10 unit. Made repairs to the wiring and replaced the fuses. Verified operation after repairs. Fuses were site stocked by the customer. Checked the York Rtu #13B for no heat. Found the inducer fan locked up and out on internal overload due to a mud daubers nest in the wheel. Removed the nest and verified operation.