Made the following repairs to the Hvac units after the preventive maintenance. Replaced the blower belts in the East and West units for the Annex gym. Replaced the furnace control board in the Annex unit #5. Repaired the condenser fan wires in the #1 condenser for the Grade school gym. Repaired the condenser fan wires and replaced the condenser fan capacitor in the #2 condenser for the Grade school gym. Secured the condenser fan wires in the #3 condenser of the Grade school gym. Replaced the compressor contactor and made refrigerant leak repairs to HP #16 for the Grade school. Leak searched and made refrigerant repairs to Rtu #29 for the Grade school addition. Replaced the compressor contactor in Rtu #17 for the high school. Replaced the belt with a site stocked spare in the boys locker room exhaust fan for the high school. All repairs were approved by Travis Laver by a email estimate.