Talk to gentlemen in office about cooling issue and he described what was going on as thermostat kept saying cooling wait. At the unit for front lobby, serial (1705168649) found compressors locked out at control board. Reset unit, compressors continue to lock out through control voltage. Began troubleshooting and under further determination found the Honeywell economizer board to being shorting out not allowing either compressor to kick on and run. Quote sent over to customer for replacement of economizer board and sensors. Unit now has economizer bypassed at economizer plug in return side.