Checked the 12,000 Btu Ramsond mini split for the warehouse IT room for condensate leak. Found the evaporator frosting on the right side due to a low charge condition causing the condensate leak. Evaporator split 9 degrees. Added R410a and cleaned the condensate drain. Evaporator split was 20-22 degrees after repairs. Repairs were approved by Allen.