Thanks for the service.
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they are secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Filter was changed on 26 Dec 20. Serviced the humidifier and changed the pad(#35). Water to the humidifier is fed from the hot water line. Also noticed they is a tankless water heater that needs to be serviced yearly. I also recommend having the quality of water tested. Poor water quality can cause issues with smaller water lines such as the humidifier. Furnace is running safely and within manufacturers specifications at this time.
Estimate for plumbing punch list
Perform an air conditioning tune up on two Lennox systems for a home in Lotawana.
In need of a plumbing inspection.
Spring A/C tune up on 2 Payne air conditioning units.
Complete two air conditioning tune-ups. Cleaned both coils, checked all safety and electrical operations.
Diagnosed failed blower motor and capacitor on furnace and cracked heat exchanger.
Performed professional all inclusive furnace tune up on both systems. Installed whole home air sanitizer.
Performed professional all inclusive air conditioning tune up.
Diagnosed and replaced failed condenser ecm under warranty.
Furnace on lennox furnace and humidifier tune up at Lake Lotawana MO.
New install furnace tune up. Another great install by our installers.