I recently had a full conversion from Oil to Gas done by the plumbers at Medford Wellington and they did a tremendous job. Mario and Max ran new piping that looks great and is out of the way and got everything up and running in a timely manner. The new burner on our Steam Furnace looks and works great! Thank you!
Found the company easy to work with and quite accommodating, though more expensive than others
Ray was efficient, informed and informative about our odd heating system.
80 Gal water heater replacement
Replacement gas furnace
Upgrade to a high efficiency Lochinvar Noble Boiler with 4 zones and an indirect fired water heater
Upgrade to a high efficiency Bosch green star Combination boiler with 3 zones and tankless water heater.
Commercial refrigeration service call for a Hoshizaki ice machine that is making no ice. Found the unit to be completely shut down. Commercial ice machine installation for a new power supply.
Commercial refrigeration service call for a Copeland walk-in freezer that will not hold temperature. Found the evap fan to have gone down. Commercial refrigeration install for a new evaporator fan
Commercial HVAC service call for a Lennox condensing unit that will not start up. Unit was making a loud buzzing noise upon inspection. Commercial HVAC install for a new starting capacitor, call is complete, unit fires right up.
Commercial HVAC service call for a Bryant RTU that is making a loud and annoying noise. Found the source to be the a fan. Commercial HVAC install for a new condenser fan
Commercial refrigeration repair call for a Manitowoc Ice Machine that is icing up. Found that the unit will not defrost. Commercial ice machine install for a new defrost timer.
Commercial refrigeration repair for a 2dr stand up True reach-in cooler. Found a pretty intense ice block, found the evaporator fan to have died. Commercial refrigeration install for a new evap fan.
Commercial HVAC repair call for a Carrier RTU that is completely down. Found the unit to be beyond repair, 30 years old with porous coils and in need of a new fan. Commercial HVAC instal for a new Carrier 5-ton RTU.
Commercial HVAC repair for a Captive Air exhaust fan that is making a loud screeching noise. Found the bearings shot. Commercial ventilation installation for a new fan motor and fan
Commercial refrigeration repair for a Ice-O-Matic ice machine that is not producing solid ice. Unit is not reading the corrected temperature. Commercial ice machine installation for a new thermostat. Unit harvesting perfect now.
Commercial refrigeration repair for a Randell Reach-In Cooler that is running warm. Found unit to have a refrigerant leak in the condenser coil. Commercial refrigeration installation for a new condenser.
Commercial HVAC repair for a Mitsubishi Ductless Split System that will not turn on. Found the unit responding to not calls to turn on, but power is flowing. Commercial HVAC install for a new control board. Unit is fully operational.