No aggravation knowledge was great Helped make big purchase easy
Clay is just a nice person and explains the problem!
Steve was very patient. And very knowledgeable about his job. An asset to moon air.
Joe did great quality work on time and budget
Polite and helpful.
Great service from Clay who is an excellent knowledgeable and experienced technician and who very competently and quickly identified and remedied the issue. Thanks to Clay! And thanks to Steve Moon for hiring great people! Thank you to everyone who helped me.
Craig never fails to provide excellent customer service. I usually stay with him and watch, mostly to learn and he is also very personable and friendly. He doesn't do a rush job, pays attention to every detail, and he noticeably takes pleasure in knowing how satisfied he is with the work he has done. He keeps our HVAC system ticking!
Installing Daikin 7 zone mini split
Daikin 2 zone mini split for pastors office and conference room
Spirit oil furnace with variable speed blower
Dent on compressor pan, return drop loose, need to replace safety trap, warranty.
Found loose connection on high voltage line connection going to furnace fixed connection and test ran operation normal at this time
Adjust main trunk dampers
Installing Gold furnace and AC replacement
Furnace rejuv. Getting a 55 degree heat rise Cleaned burners and flame sensor. Changed filter supplied by customer. Checked eletrical conections. Draft mor amps 1.3 blower motor amps 5.1 voltage enhancement system read 8.5 our of 10 Chang it wiped down furnace. Checked tubing for clogs cleaned blower Checked heat exchanger and found no areas of concern.
No A/C, checked system and found that the voltage enhancement system had failed, factory spec 30/5, actual 3.3/0, installed replacement and test ran, operation normal at this time.
Club service A/ C, test ran system, indoor air filter is very dirty, customer will change, compressor run load amps factory spec 10.9, actual 6.3, outdoor fan full load amps factory spec 1.1, actual. 9, 20 degrees delta t, operation normal at this time.
Paul stopped and got a material list for install on 9/22
Gold furnace and AC replacement with duct cleaning and Air Ranger
Installed new control board. Test ran 10 minutes maintained temp. System normal operation at this time.
Outdoor unit crawl space 5/35. Fixed a wiring connection. Cleaned unit. Outdoor unit attic read 5/39.9. Checked wiring conecctions. Cleaned unit. Outdoor unit mini split coil cleaned and connections fine. Indoor unit crawl space 60 supply 76 return and 16 delta. Voltage enhancement system read 9.9 with a factory setting of 10. System normal operation at this time. Changed nozzle, strainer, gaskets and filter for oil boiler. Bled air out of system, test ran 10 minutes. System normal operation at this time.
Cleaned flame sensor and flame sensor. Wipe down furnace inside and outside. Blower wheel is clean checked eletrical conections. Did gas leak check found small leak at orfice tighten orfice. Checked heat exchanger found no areas of concern. Getting 55 degree heat rise draft motor amps 1.6 blower amps 4.3 operation normal at this time