Craig was on time. Very efficient and very polite and friendly. Would like him to be our regular guy
Well the price was way to high because he did not do any work to the heater
Keith was very patient and helpful. He answered all questions we had and put us at ease. He’s a valuable asset to the company. He was honest and we appreciated that.
Excellent , patient and explains and answered my questions. Addressed all my concerns
Craigs a very nice young man. He reviewed what he did he’s polite
Greg, the technician, is a regular at servicing our heater and a/c. Very prompt and neat. Always wears his protective coverings. Spends a good amount of time to do a thorough job and complete check and service of the systems. I always recommend Moon Services to anyone looking to have work done on their heating and air conditioning systems.
I wouldn’t call nyother company for service. Moon Air is efficient affordable and friendly The persons who service our have were on time,polite and efficient
No A/C, outdoor pumping system not running, checked and found that the outdoor voltage enhancement system had failed, factory spec 45/5, actual 4.1/1.2, installed replacement and test ran, compressor run load amps factory spec 13.6, actual 8.3, outdoor fan full load amps factory spec 1.1, actual. 8, suction 135, liquid 270, operation normal at this time.
Gold heat pump replacement
Returned and placed remaining coolant into the outdoor system, removed indoor heat exchange system and installed replacement, vacuum to 537 mircons and test ran and recharged system, suction 119, liquid 266, operation normal at this time.
2 ton heat pump.
No A/C, low cooing, checked system and found that it low on coolant due to several leaks on the indoor heat exchange system, checked with factory and is out of warranty.
Ac club rejuvenation, delta t 13, changed filter old one was dirty, voltage enhancement system 4.66fp 5 factory in spec, cleaned ez trap, checked blower wheel spins with no restrictions and clean, checked all board connections everything is secure and tight, no issues. Outdoor unit, voltage enhancement system 43.8fp 45 factory 4.8fp 5 factory fan in spec. Checked all board connections,bottom of unit very clean and coils also clean. No issues
Club ac rejuvenation, changed air filter, 18 delta t, voltage enhancement system 18.85fp 20 factory, checked all board connections, checked blower wheel spins with no restrictions and clean, system sounds good, no issues. Outdoor unit, voltage enhancement system 42.08fp 45 factory, 4.68fp 5 factory fan. Checked coils they are clean, bottom of unit minimum leaves, no issues system sounds good, wd40 wipedown on unit.
Thoroughly Cleaned indoor heat transfer system. Removed air movement system and cleaned. Removed baffle from indoor heat transfer media and cleaned. Cleaned cabinet insulation. Cleaned exterior of cabinet.
Checked mini split system.found system low on refrigerant. Complete leak check found leak at outdoor heat transfer media.customer authorized repair, evacuated and refill system. 25o delta T. Air filters clean.
Club ac rejuvenation, checked air filter, delta t 20, voltage enhancement system 11.8fp 12.5 factory. Let customer know it's getting weak and will want to replace soon, checked board connections, checked blower wheel spins with no restrictions. Outdoor unit, voltage enhancement system 37.7fp 40 factory 4.71fp 5 factory fan. Opened unit and cleaned out leaves in it, coils in good shape and clean. No issues.
Club ac rejuvenation, Supply has a temperature of 52 degrees. Return has a temperature of 70 degrees. Delta t of 18 degrees. Indoor voltage enhancement system is reading 9.7uf and with a factory spec of 10uf it is within the allowable fault. All indoor control board connections are good. Air filter is clean. Checked evaporator coil and pan both are clean and looking good. Cleaned out ez trap with the provided brush. Wd40 wipe down of the indoor unit. Outdoor voltage enhancement system is reading 44.2/5uf and with a factory spec of 45/5uf it is within the allowable fault. The electrical gateway is without any pitting or burn marks and looks. Cleaned out the outdoor electrical compartment. Cleaned off outdoor coil as well as the bottom of the unit to clear out all of the drain holes. Wd40 wipe down of the outdoor unit. System is operating normally at this time.
Air conditioning rejuvenation
Checked air conditioner. Cleaned outdoor heat transfer media. Air filter clean. Cleaned interior of indoor heat transfer media. Flushed water removal system. Tested secondary emergency shut off. OK. Recommend air movement system, and indoor heat transfer media be cleaned.
Club service A/C, changed customer supplied air filter, test ran system, 21 degrees delta t, compressor run load amps factory spec 14.1m actual 7.3, outdoor fan full load amps factory spec 1.5, actual 1.1, voltage enhancement system factory spec 45/5, actual 45.5/4.9, operation normal at this time.
Noise from system, customer had shut off power reset and system started, told him not to turn off power if it happens again,