Tom was on time and professional!
We had a great experience today having Tom come out and service our units. He was very knowledgeable and professional.
tech was able to find a problem and show me what was wrong with the part, that he had to replace.
Tom, service tech, and the support staff were amazing. Tom explained everything, complete with pictures. I prefer to work with family-run businesses whose reputation, work-ethic and value for service are primary consideration. This was AMAZING!
Response from Morehart Air Conditioning & Heating:
Thank you so much for you feed back! We value and appreciate you as our customer!
In Peoria, Az off of 91st and Lake Pleasant Parkway. Upon arrival found system on lockout for short cycling and high pressure discharge. Found fan motor locked in place. There is something wedge between blade and shroud for fan. Removed and reset system. Unit working properly charge in second stage at 131/298 psig. Recommend replacing 45uf capacitor and OEM condensing fan motor.
In Peoria Az servicing a customers new Amana system we installed 4 months ago. System is running properly and install looks really good. Changed the customers filters everything is running properly.
In Peoria Az servicing a customers Goodman furnace. Cleaned out furnace cabinet. Removed and cleaned the flame sensor. Checked all safety equipment on the furnace. ready for winter.
In Peoria Az acid washing an indoor coil on this package system. Washed out 5 times with coil acid all cleaned out now, also removed and cleaned the blower assembly nothing better then clean air in your house.
In Peoria Az installed new 2 ton 18 seer Samsung Ductless system head unit with condenser hooked up copper lines pressure tested sat on vacuum for 30 minutes ran high volt wire to condenser and ran connection wire ran pvc down the house tested system cleaned up job site.
In Peoria, near West Port Royale Lane and North 88th Lane performing Fall preventative maintenance on an 2 Amana split systems. Completed services for 2 systems. Home was vacant at time of services and systems were off. Turned systems off after servicing. Upon departure, systems are running properly and within manufacturer specifications.
In Peoria, near West Beryl Avenue and North 67th Avenue performing Fall preventative maintenance on an American Standard gas pack. Completed service in accordance with maintenance checklist. System is 12 years old and runs on R22; recommend monitoring and budgeting for replacement. Upon departure, unit is working within manufacturer specifications.
In Peoria, near West Laurel Lane and North 87th Avenue performing Fall preventative maintenance on an Amana furnace. Completed maintenance service in accordance with maintenance checklist. System working properly upon departure. Left estimate to replace water heater. Recommend monitoring and budgeting for replacement; it is 16 years old.
In Peoria, near West Salter Drive and North 89th Avenue performing a diagnostic on an Amana split system. Upon arrival, cycled unit into cooling mode. Checked refrigerant levels and found below specification. Began inspecting and looking for leak. Found piston fitting loose. Retightened fitting and recharged system. Upon departure, unit is working properly and within manufacturer specification.
In Peoria, near West Puget Avenue and North 101st Drive performing a combo preventative maintenance on a Goodman split system. Cycled system on into cooling and heating mode. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures. Acid washed outdoor coil and rinsed. Checked attic air handler. Drain line is clear and secondary drain pan is in good condition. House and system are newer. Unit is running properly and within factory specification.
In Peoria, near West Planada Lane and North Paseo Laredo Lane installing a new blower motor. Installed new OEM ECM blower motor from Carrier. Cycled system on in cooling mode; blower is running properly. Checked condenser, volt and amp draws are good. Freon levels are good as well. System is running properly and within manufacturer specifications, upon departure.
In Peoria, near West Golden Lane and North 114th Avenue performing Fall preventative maintenance on an Amana gas pack. Completed service in accordance with maintenance checklist. Upon departure, system is running properly and within manufacturer specifications.
In Peoria, near Westwing Parkway and North 89th Lane performing a dual preventative maintenance service for 2 units. Replaced 10uf capacitor at time of service. South condensor motor is starting to chatter on startup, but amp draws are within manufacturer rating. Recommend replacing motor in the next year. Left estimate to replace systems at time of service.
In Peoria, near West Brown Street and North 96th Avenue performing seasonal preventative maintenance on a York package heat pump. Completed service in accordance with maintenance checklist.
In Peoria, near West Bell Road and North 88th Drive performing a diagnostic on a commercial system that is not cooling. Fan motor wires disconnected from testing cap. Reconnected and tested system.