In Queen Creek, AZ: DIAGNOSTIC- Upon arrival, found Schrader valve leaking. Unit is a little bit low on charge 132/399 95 SLT. Added 1 pound of R410A. Set charge at 142/422 85 degree SLT. Splits are 58/78. Customer is concerned with build up on registers and wants vents cleaned. Changed filters during service because they were very dirty. Listed an estimate for duct cleaning and dryer vent cleaning. Unit splits are 20 degrees, I don't believe home can maintain 74 degrees during the hottest part of the day. Would recommend insulating home, windows, etc. Left estimate and service completed.
In Queen Creek, AZ: FREE ESTIMATE- Provided customer with an estimate for new mini split system. Estimate given; service complete.
In Queen Creek, AZ: DIAGNOSTIC- On arrival, found system running. Customer had system set for 77 degrees. Checked splits: Return 77/Supply 58. Checked Freon levels. Suction 125/Liquid 350. Checked volt and amp draws. Compressor: Rated at 17.9/Actual 13.76. Outdoor fan motor Rated 1.1/Actual .92. Found contactor very burnt and pitted; hard start kit is at 0.0 MFD Rated at 189-227. Need new single pole contactor and new hard start kit. Installed parts. System is running properly. Checked attic furnace and duct work looks good. No other issues found. Service complete.
In Queen Creek, AZ: Estimate- Morehart AC to install and furnish 3.5 ton package heat pump system. To include new disconnect whip kit, thermostat, and drain line. To hook up to existing ducting, low volt, and high volt. Price covers tax, installation, and removal of existing equipment.
In Queen Creek Az servicing a customers system. Checked volt and amp draws. Cleaned out control cabinet and tightened electrical. Checked Freon levels. Acid washed the outdoor coils and changed the return air filters.
In Queen Creek Az servicing an Amana system we installed 5 years ago. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels. Acid washed outdoor coil and changed return air filters. Unit is running to factory specification at this time.
In Queen Creek doing a tune up on a Goodman split system! Unit is in great condition and is cooling properly!