In San Tan Valley, AZ: PREVENTATIVE MAINTENANCE- Cycled system on into cooling mode. Checked volt and amp draws; all in factory specification. Cleaned and tightened electrical connections. Checked Freon levels and pressures; also in factory specification. Acid washed outdoor coil and rinsed. Changed return air filters and checked splits. Return 76/Supply 57. Hard start kit is very hot and is low on MFD. Recommend new hard start kit. *Installed new hard start kit. Cycled system back on. System is working properly and within manufacturer specifications. Service complete.
In San Tan Valley, AZ: CYCLED SYSTEM ON IN COOLING. CHECKED VOLT AND AMP DRAWS, ALL IN FACTORY SPECIFICATION. CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. CHECKED FREON LEVELS AND PRESSURES, ALSO IN FACTORY SPECIFICATION. (SEE COOLING CHECKLIST FOR DETAILS). ACID WASHED OUTDOOR COIL AND RINSED. CHANGED RETURN AIR FILTERS AND CHECKED SPLITS, RETURN 77 SUPPLY 57. SYSTEM IS RUNNING PROPER AT THIS TIME.
In San Tan Valley servicing a newer Carrier . Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures. Acid washed outdoor coil and rinsed and changed return air filters.