In Scottsdale, near East Chama Road and North Hayden Road performing a diagnostic on a Trane furnace. Upon arrival, found transformer not putting out 24 volts. Installed new transformer with fuse block. Cycled system on and found compressor not coming on as run capacitor is dead. Installed new capacitor and upon departure, system is working properly and within manufacturer specifications.