In Wickenburg, near West Wickenburg Way and North Vulture Mine Road performing a diagnostic on a Carrier package heat pump. Found that the run capacitor was bad; installed new run capacitor on blower motor. System is running within manufacturer specifications upon departure.
In Wickenburg, near West Wickenburg Way and North Vulture Mine Road performing a diagnostic on a commercial Carrier package heat pump. Upon arrival, found thermostat to be blank due to blown fuse; capacitor blown apart and motor grounded out. Installed new 1/4 Horse 1075 460 volt motor and new 7.5/440 run capacitor with new fuse, and system is now running properly and within manufacturer specifications.
In Wickenburg, AZ: Checked furnace and coil in the garage. Supply is sealed very well and clean. Gas line is tight and sealed. PVC flue piping is correct and glued. Drain line for furnace and coil are plumbed and glued properly. Cycled furnace on, all working properly. Cycled cooling. Checked condenser, hooked up gauges; pressures are set proper. Suction 130 Liquid 357. Disconnect installed with new whip and proper. Install looks very good with no issues. Removed program off thermostat. Customer just wants easy. Completed QC.
In Wickenburg Az servicing a customers 12 commercial systems on the roof. Found a few repairs that were needed. Changed parts and installed new filters all ready for summer.
Installed new Rheem 40 gal electric water heater
In Wickenburg Az servicing a customers Trane system. Checked volt and amp draws. Checked Freon levels and pressures. Changed return filter and acid washed outdoor coil and rinsed.
Beautiful day for services! In Wickenburg performing preventative maintenance on 4 Amana systems!
Performing routine maintenance on twelve carrier HVAC equipment in Wickenburg .
In Wickenburg installing filters on a customers commercial building that has 12 air conditioning systems!