My technician was wonderful, very skilled and he diagnosed the problem immediately and fixed it very quickly! I am so grateful! I definitely recommend this company.
Replace 3 old toilets, replace upstairs sink and drain, reroute AC condensate line to stop leaking inside wall
Upon arrival the technician went over the system top to bottom to find any reason why the system would shut off in the middle of the day. The technician was unable to determine any reason why the system was shut off and heat of the Day. The customer stated that his nest thermostat had an eco feature, this feature would since if anybody was home, And if it had nobody that crosses sensors within an hour it was shut off and called the temperature at 76. But the customer was noticing that it was keeping it at 80Â° constantly. The technician recommended switching off Eco mode for now and testing to see if this solves the issue.
Upon arrival the technician found that the system upstairs had a clogged primary drain line. The technician vacuumed out the drain line from the sink drain. System working properly at this time.
Customer needs ro housing and new tank didnâ€™t have all parts also gas leak under sink and dishwasher referred to water Mediation to remove sheet rock and cabinet tree to inspect plumbing for leaks did not see any active leaks while I was there inspecting underneath kitchen sink everything was just wet
Upon arrival technician inspected the system and found that the system is a single stage system with three zones. Which is causing an abundance of water to build up in the drain line, with the addition of the algae this causes a lot of issues.The minimum work that needs to be done is to replace the drain pan and drain lines. In order to solve all the issues, the customer will need to replace the system with either two systems or an 18 seer to 20 seer system.
Install new Navien tankless water heater. My Guys will include at no additional charge an upgraded power supply outlet local to the water heater as well as an automated Flood Stop alarm to prevent potential for flooding and a Scale RX sediment filtration device at no additional costs. A roofer will also need to come out and reseal the roof jack, this is also at no additional costs.
Upon arrival technician found that the system was low on 410 a refrigerant. While charging the system the TXV locked up and shot the pressure up to 600 psi on the high pressure side. The technician called Charlie, Charlie stated that he would like to replace the coil so it will solve all the issues.
Upon arrival the technician spoke with the homeowner, the homeowner explained that his master bedroom closet and master bedroom bathroom does not cool as well as the front two left bedrooms .. The technician went into the attic and found that the affected rooms are coming off ducks that have multiple wise and are losing 90% or more of the airflow. The technician recommends running new ductwork to these rooms and replacing the Plenum so that all of the ductwork will fit on the system. The homeowner stated that he will talk to his wife and get back to us with a decision.
According to the office the customer set the appointment to begin at 5:30 when they got home from work the technician arrived at 5:25. The technician knocked on the door, after waiting a few moments the customer came over the ring camera system and stated that he wouldnâ€™t be home until 7 PM. Office stated that they would reschedule the appointment.
Replace pvc toilet flange existing one is cracked toilet pipe is not secure will need to secure pipe and install new flange. Will need to peel out pipe from floor pipe
Customer needs price for us to install a solid 1 piece shower fiberglass going to coburns to find price
Need to make estimates later on
Upon arrival the technician found that the system is low on r410a refrigerant, the system is currently freezing up. The technician for formed a leak search and picked up a hint of refrigerant in the coil. The technician believes that the coil is leaking refrigerant. And needs to be replaced.
Upon arrival technician spoke with the customer, the customer explained that they are moving out of the house and need some repairs done before selling. One of the two water heater tanks are not working due to the pilot light going out. This tank is the second tank in sequence, which means that the hot water goes into this tank to cool and be used. This hot water heater will need to be replaced. The customer also stated that the upstairs toilet needs to be replaced. The customer has already purchased the toilet. Also the garbage disposal needs to be replaced.