Friendly knowledgeable employees
The technician returned and installed pool system backflow. Backflow working properly at this time.
Upon arrival the technician disconnected the hose to the hose bib. The technician found that the hose, hose bib, and backflow preventer is completely bone dry. The technician turned on the water three times and turn off the water to successfully shut off the water completely without any issues. If the hose is still connected to the hose bib when the water is shut off all the pressure in the water will rush out of the backflow preventer. The technician believes that this is the experience of the customers having. Because the technician upon six attempts to have the hose bib leak, The technician was not able to repeat the issue that the customer is experiencing. Hose bib and backflow preventer working properly at this time.
I found arrival technician found that the system for the right side of the home currently has intermittent compressor power issues. The system is overheating due to the age, condition, and position of the system. At the very least the condenser will need to be replaced.
Estimate to replace 50 Gallon tall natural gas water heater, two hose bibs, flush both systems condensate drain lines and perform a full service on each system as well as installing two vacuum breaker anti - syphon to the new hose bibs.
Upon arrival the technician spoke with the customer, the customer explained that he had a realtor inspector come out and inspect the house, because the house is being sold. The inspector stated that a few items need to be taken care of including the fact that the water heater on the left was not lighting. The air conditioning systems needed to be inspected and serviced, having the drain line blown out. As well as the back flow preventerâ€™s on the hose bibs on either side of the house need to be repaired. the technician first checked the water heater ensuring that the water heater would light, after several unsuccessful attempts the water heater finally lit, the technician set the water heater to warm. The technician then inspected the backflow preventers, and found that both set screws are seized with rust as well as rust has made its way into the screwdriver channel. The Backflow preventerâ€™s are seized to the hose bibs so the hose bibs and the back flow preventerâ€˜s will need to
Upon arrival technician found that the primary drain line was clogged which was causing a drip into the secondary drain pan. After leaving the drain pan the secondary line goes over the attic to the backside of the house and sits above the soffit. The water coming out of this drain line is just dripping onto the soffit. Due to the fact that upon repainting and sealing the home, someone came in and sealed the secondary drain line hole. So now the water has nowhere to go and itâ€™s just sitting in the soffit dropping out of cracks. The technician who are the primary drain line.
Install new navian tankless water heater With a flood stop. Also will need a roofer to install new flashing cap collar and eliminate exsisting fresh air intake pipe. Install scale rx water filter. Also set up for ac tech to come out and do a ac tune up including coil cleaning inspection of Freon pressures and blow out ac drain and replace hose under sink. Installed new unit no issues found after testing
Upon arrival technician found that the homeowner has 1 inch filters and 4 inch media filters. The filters were currently clogged. The technician removed the bad filters and replaced with a good filter. System working properly at this time.
Upon arrival technician found that the electronic gas valve was turned off. The technician turned on the gas valve and tested the system. System working properly at this time.
The technician arrived and inspected the unit. System is properly charged and pushing out an 18Â° delta T. The technician also picked up a check for the remaining amount.
Upon arrival technician found that the condenser has grounded out. The technician spoke with the homeowner about replacing the condenser and the coil, the coil and condenser were put in at the exact same time. So the homeowner would like to replace both coil and condenser to ensure proper cooling. My Guys Heating And Air Conditioning will be installing a coil and condenser for Tim Graves on Saturday, August 27, 2021