Found faulty pressure switch in homes water delivery system. Replaced switch with 40/60 switch. Customer adjusted well tank in casing to 38psi was at 28psi. Warranty on pressure switch only. Reccomend replacement of pump due to age and preventive. Also relocation of well tank to inside home and redirect power supply to accommodate moving of tank.