Performed cooling inspection on one system. Checked inside and outside units, checked electrical components, checked drain line and drain pan and checked the charge. Noticed outside condenser coil is dirty and capacitor was blowen. Replace (1) 40/5 uf capacitor and washed outside condenser coil. All working ok at this time.