Response from MY PLUMBER HEATING COOLING & ELECTRICAL:
Thank you for the great feedback. We will be sure to relay these comments back to the technician and his manager. As always thank you for your continued loyalty and support. We hope that in the future if you or anyone you know needs plumbing or HVAC service, you will send them our way. We will make sure they to receive the excellent quality of service you received on our most recent visit. Kind regards, The My Plumber Heating and Cooling Team
Supply 51 Return 70 Filter homeowner will replace herself Condensation line good Uv not operational Blower wheel good Blower motor capacitor 7.4 Blower 1.3 Outdoor coil needs cleaning Compressor 5.8 Fan .8 Contactor operational Capacitor 33.6/4 replacement Running pressures 410a 127 saturated temp 43line temp 61 283 saturated temp 92 line temp 82 Subcool 10 Superheat 17 No lose or damage wiring Talk with homeowner regarding uv bulb declined for now Thank you for your business
The technician did not turn the switch to automatic when he was finished last time Tested that both pumps would cycle and they did. As of this point the system is working as it should
Went to dewinterize customer house after turning back on water check all fixtures to make sure no air radar was clogged only for one exception 40 gallons propane state water heater was not staying lit that was installed by us in 2017 may customer could not find receipt to no if heater is still under warranty but finally after office located it’s on file after 1 hour plus
Snake upstairs toilet ( Toto ) 6’. Removed blockage successfully. Tested everything working properly.$35 coupon discount . No warranty on toilet stoppage.
Installed valve and replaced a section of 3/4 cold line for kitchen sink.
Replaced flapper,handle, supply line,and fill valve