Over $730 to replace a toilet bowl flushing mechanism and an under sink leak.
Response from MY PLUMBER HEATING COOLING & ELECTRICAL:
Thank you for the great feedback. We will be sure to relay these comments back to the technician and his manager. As always thank you for your continued loyalty and support. We hope that in the future if you or anyone you know needs plumbing or HVAC service, you will send them our way. We will make sure they to receive the excellent quality of service you received on our most recent visit. Kind regards, The My Plumber Heating and Cooling Team
The service was quick and I am hopeful done very well. My concern is as a Priority Member, $40 coupon is on the website for Prority Members but not applied. I would like to have this applied to my bill. I believe 10 percent and 5 percent was applied based on $83.00 deducted from total. I asked for the FULL amount but it got uncomfortable. I did not want a confrontation. Request the Manager to take action and CREDIT my account please for the full $40 discount for VIP customers on any service. I also called and asked to speak with the MANAGER regarding my problem. Thank you,
Install warranty compressor for tran unit with tech Jesse W. Recovery the Freon and then replace the compressor and filter dryer and ran the nitrogen for leaks search and then run the vacuum to get 250 on micron gauge. Added 12 lb R410 to get proper super heat and Subcooling.
Upon arrival assessed job ,Recovered Refrigerant (8lb’s) factory charge .(12lb’s 1oz) once compressor arrived,found replacement compressor sweat,VRS -Rotolock,Repiped as needed,Replaced filter drier,pulled deep vacuum,weighed in factory charged,start and checked system
Replace old laundry faucet with new moen laundry faucet To stop faucet from dripping. Two 1/2” shut off valves install also. No leaks and the faucet is working to code.
Braided poly supply lines to entrance level bathroom faucet were frozen (exterior wall).
Replaced hot and cold valves to washing machine. Replaced Moen cartridge.
major rebuild also replace 11/2 trap with tail peice for lav in mb first lav on right hand side
l snaked/cleared kitchen sink drain galvanized around 25 ft pulled back gunk sludge
Ran the k50 through the floor drain to clear.
Replaced straight stop for upstairs hall bathroom toilet. The floor beneath the w/c is nonexistent. There's no point in trying to set a toilet, no way to secure the flange
Replaced w/o gasket and shower head/arm in upstairs hall bathroom tub
Repaired 3/4" waterline behind water heater