Did a great job.
Found pressure switch bad on well tank Installed new 30/50 switch and nipple
Installed 40 gal electric water heater 5 gal expansion tank, customer financed through Wells Fargo
Arrived to customer hot water heater not installed correctly by husband. Diag2 fee to find heater not wired properly and thermostat control box malfunctioning. Gave customer option to either order new control box or return water heater and have my plumber install new 50 gallon w/h with 5 year warranty up to code. Or have flow tech installed with 10 year warranty. Electric w/h
install 86g well tank. Test and install new main water valve on well tank.