Completed pulling of 3 hp pump to check why pump was not operating. Ohm readings were not consistent on legs. Checked motor windings all checked out. Determined that wire had shorted. Replaced 10/3 well wire. While gathering old wire found burned out section of wire. There is no visible damage in area of burnout. Reset pump and tested. Original warranty is still valid. Customer is super pleased with our performance. Tech requesting warranty pay.