I was so pleased with how professional and friendly they were.
When I arrive homeowner explain that outdoor unit was running but indoor wasn’t Homeowner son explained that he smelled a weird smell the day the motor stopped running Check voltage , low voltage was there 26 high voltage good as well 120 Control board operational,notice blower was bad Performed full 360 evaluation and noticed that capacitor on outdoor unit was failing Replaced talk with homeowner regarding system using R22 Declined upgrading at this time added dep999 for future upgrade Thank you for your business business have a great holiday
check the wiring and temperature all are in good condition, all safeties are ok, Clean the Outdoor condensor coil and change the dryer vent pipe.Refrigerant charge is ok.
Psi90replease expansion tank and pressure relief valve on gas epwater heater recommended to install pressure valve no warranty because high pressure I dee plumbing evaluation
Plastic drain valve snapped off old water heater and leaked out. Install new 40 gallon natural gas water heater with expansion tank and isolation valves. Customer chose NO WARRANTY option.
I installed a new fill valve. One year warranty.
Replace water main interior shut off valve and minor rebuild on m/b toilet.
Kitchen sink stoppage. Pulled back grease but customer stated that she threw chicken breast down the line. Snake line to 50 feet did hit anything. Please call to set appointments she said was going to set it when she has the chance but if someone could call her Incase she forgets that would help.
I inspected Furnace and ac system to include: R-22 piston -All electrical wiring, motors, and components. -All safeties ok -drain is clear and functional -coils are clean -Refrigerant charge is good Oddb 70 Iddb 72 Contactor was burned and pitted. I replaced Blower motor is starting to fail, recommend Ez- Trap drain protector M Want to get one more year before replacing.
replace leaking valve on water heater install anti scale water system flow tech sing costumer for priority club 2 years warranty parts and labor
install a gerber white round in p/r.
snaked /cleared laundry drain copper around 15 ft pulled back lint also snaked/cleared lavatory sink drain around 10 ft pulled back lot sludge gunk and replaced trap j bend 1-1/2 satin same lavatory sink basement sold bio clean
Hydrojet done. Jetted kitchen sink line to main line line. Line is good.