ESTIMATE TO PERFORM PREVENTATIVE MAINTENANCE SERVICE ON 2 COMMERCIAL WATER HEATERS FOR THE NORTH DORM.
ESTIMATE TO REPLACE GAS VALVE AND THERMOPILE GENERATOR FOR GAS FRYER.
Commercial fuel line to commercial kitchen fryer. Pilot stays on until thermostat is turned on then the pilot goes out. Replace gas valve and thermopile generator for gas fryer.
ESTIMATE TO PROVIDE LABOR TO TROUBLESHOOT VULCAN GAS FRYER
Commercial plumbing service. Replace commercial water heater.
ESTIMATE TO REPLACE LEAKING COMMERCIAL HOT WATER HEATER IN ADMIN MECHANICAL ROOM.
Clean and Sanitize ice maker
Commercial heating repair. Replace safety relief valve for booster heater.
COMMERCIAL PUMP REPAIR. REPLACE CONTACTOR AND OVERLOAD RELAY FOR JOCKEY PUMP.
COMMERCIAL HVAC REPAIR. REPLACE 3-WAY VALVE, OPERATOR, BLOWER MOTOR, CAPACITOR, BLOWER WHEEL, MOTOR MOUNTS AND FAN HOUSING.
Commercial plumbing service. Clean and sanitize ice maker.
Work performed on 3/23/2021 Vulcan stove back stoves next to each other the one on the left needs 1- transformer and burner blower complete assembly with wheel may not come apart, due to age also other work may be needed need blower to operate for next steps of operation blower has 110 volts to it but not working motor is shot. Also needs light switch it is broken. Note photos are in photo file. These are the stoves no model or serial #. Scotsman ice machine was off turned on making ice. Was locked on code 6 this is the swing door that deflectâ€™s ice into chest area it was stuck open take side off machine and clean and reinstall. Let machine make ice. Needs to be Sanitize Grill bye front counter replace thermocouple pilot stayed lite and grill came on let run to burn off. It is working as of this date Flats top grill pilot was out and Joel lite the pilot it working Single fryer up front is working. Joel tried it. The one on the right has a crack in the fryer leaking grease unsa
Estimate to repair dorm fan coils.
Work performed today February 10, 2021 South dorm section A Rm#228 bleed air working Rm#224 needs complete 3way valve blower motor/wheel and plastic cover around motor I believe the last time I did one Rm 246 same as 224 South dorm section B Rm#250 student in rm could not get in Rm#146 complete 3 way valve Center of dorms front doors Rm# 105 ,103 these to offices are on building central heating system the water temp in running at 157 degrees boilers are set about 160 to 170 degrees boilers are running not cycling water temp needs to be raises to 180 degrees and the out side air damper needs to be shut down some with temps this cold outside try to talk to Nova he played dumb I said forget I will put it in my report this gets changed on the building computer system I donâ€™t have access . All Electric make up heaters on all out side walls and by front doors breakers where in off positions Nova played dumb about this too! South dorm section D Rm# 193 and 181 did not get to ran out of tim