As always, the service technician was on time, courteous, and professional. He was ready to answer any questions I had. I've was pleased with the service.
I am very pleased with service I got. The young man was very polite and explain every thing he did .I give him an A+.
Taylor was very professional. He explained what he was doing and why.
They did great on the installation and follow up. Also they were awesome when theyvame out to fix a gas leak that was not related to their work.
I appreciate the service plan offered and I am aware that my system will be much more efficient if it is properly maintained
We've been using Perfect Service Heat and Air for approximately 6 years . They put in our unit and have serviced it every six months since. Malays great service and the price is right! Highly recommend them!
Response from Perfect Service Heating & Air:
Thank you for your review. We are happy you have picked us to be your hvac company. We look forward to providing you with great service for years to come!
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK CONDENSER COIL. INSTALLED 3.5 TON AC/FURN/COIL. MADE SURE SYSTEMS WAS INSTALLED PROPERLY. CHECK ALL ELECTRICAL CONNECTIONS, CHECK DRAINAGE, CHECK FREON LEVELS, CHECK VOLTAGE AND AMPERAGE ON MOTORS. MADE SURE WORK AREA WAS CLEAN WHEN LEFT. EVERYTHING IS RUNNING GREAT.
INSTALLED UV AND FACT WTY COND FAN. MADE SURE EQUIPMENT WAS INSTALLED PROPERLY. MADE SURE WORK AREA WAS CLEAN WHEN LEFT. CHECK ALL ELECTRICAL CONNECTIONS, CHECK DRAINAGE, CHECK AIR FLOW. EVERYTHING IS RUNNING GOOD.
CAME OUT ON SERVICE CALL. FOUND THERE WAS A WATER LEAK. FIXED THE LEAK, CHECK AIR FLOW. EVERYTHING IS WORKING GOOD.
Service work performed for the heil 2014 air condensing unit with heat pump, checked ducts for build up, no repairs needed.
Service work performed for the Heil 2012 air condensing unit with heat pump.
Cleaned burners and checked gas lines for leaks, checked air filters for wear.
Cleaned and safety checked condensation drain, cleaned ducts.
Cleaned condensation drain checked ducts for build up, no repairs needed.
Checked ducts for build up, cleaned condensation drain with Zep con-coil cleaner. Cleaned air filters, no repairs needed. Best HVAC in Adamsville.
Service work completed for the Heil 2011 air condensing unit with Zep con-coil cleaner. No repairs needed. Best HVAC in Adamsville.
Cleaned and sanitized the Heil air condensing, cleaned air filters. customer satisfied. Best HVAC company in Adamsville, Al.
Performed regular maintenance work for the package unit. Best HVAC company in metro Birmingham.
Service work completed for the heil air condensing unit with Zep con-coil cleaner.
Checked heat exchangers for cracks, adjusted blower motors, customer satisfied with service work.
Checked air filters and thermostat. Checked home for proper air flow