AJ done an excellant job and with pride in his work
Skyler was polite and through. I appreciated attitude
CAME OUT FOR ESTIMATE ON EQUIPMENT. INSTALLED 4 TON HP/AH CONVERSION 7 YR P/L. MADE SURE EQUIPMENT WAS INSTALLED PROPERLY AND WORK AREA WAS CLEAN WHEN FINISH, CHECK BURNERS AND BURNER OPERATION. CHECK CONDENSER COIL. CHECK THERMOSTAT, AIR FILTER, AIRFLOW, AND ALL ELECTRICAL CONNECTIONS, EVERYTHING IS RUNNING GREAT,
1ST CLEAN AND CHECK FOR 6YR HEATING UNIT UNDER SERVICE AGREEMENT. CHECK MANIFOLD GAS PRESSURE AND FOR PROPER VENTING. LUBRICATE ALL NECESSARY MOVING PARTS, AND ADJUST BLOWER COMPONENTS. CHECK BURNERS AND BURNER OPERATION. CHECK THERMOSTAST, AIR FILTER, HEAT EXCHANGER, HIGH LIMIT CONTROL, FAN CONTROL, ENERGY CONSUMPTION, HUMIDIFIER, AND ALL ELECTRICAL CONNECTIONS.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK AIR FILTER, CHECK CONDENSER COIL, CHECK COMPRESSOR DELAY SAFETY CONTROLS, CHECK DRAINAGE, CHECK FREON LEVELS, CHECK DRAINAGE. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK CONDENSER COIL, CHECK DRAINAGE, CHECK FREON LEVELS, CHECK ALL ELECTRICAL CONNECTIONS, CHECK AIR FILTER. ADJUST BLOWER COMPONENT, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING IS RUNNING GREAT.
Completed clean and check for the Heil 2014 80% furnace. Checked manifold pressure, checked humidifier.
Checked ducts for build up, cleaned condensation drain with Zep con-coil cleaner. Lubricated all moving parts. Best HVAC in Adger.
Service work performed for the Heil 2014 air conditioning unit with Zep con-coil cleaner. no repairs needed.
Cleaned and sanitized the Heil 2013 air conditioning unit with Zep con-coil cleaner, no repairs needed.
Service work performed for 2009 Heil air conditioning unit with Zep con-coil cleaner. Cleaned condenser coil and condensation drain.
Cleaned and sanitized Heil air conditioning unit with Zep con-coil cleaner, No Repairs needed.
Clean and check done for heil 2012 package unit.
Check and clean on a 3-year-old Goodman. Check the pilots and igniters to make sure the furnace cycle turn on and off as it should. Check the thermostat to make sure the heat don't come on too soon or stay on too long.
Heat maintenance on a 2-year-old Trane. Check heat exchanger to assure proper fuel combustion and avoid the possibility of creating carbon monoxide.
done service in ADGER for a customer on the heat and they renew their heating and air conditioning maintenance contract
yesterday one of our new customers was getting air conditioner service for their yearly contract