Glad they came out and checked since something had gone wrong but still under warranty.
right on time and told me everything he was doing and looking for. Thanks.
Same as review title.
Everything went great "once" the serviceman got there.I was told 4pm or so..he got here at 6:30pm..Still I am satisfied with the service..
David spent 2 hours checking out everything about our unit. Very satisfied with his service, friendliness and explanation of what he had found and how to fix it. I have asked for him to come back each time.
INSTALLED 4 TON HP/AH W/ T-STAT. MADE SURE SYSTEM WAS INSTALLED PROPERLY, CHECK ALL ELECTRICAL CONNECTIONS, CHECK DRAINAGE, CHECK THERMOSTAT, CHECK VOLTAGE AND AMPERAGE ON MOTORS, CHECK FOR PROPER ENERGY CONSUMPTION. MADE SURE WORK AREA WAS CLEAN WHEN LEFT. EVERYTHING IS RUNNING GREAT.
CAME OUT ON A SERVICE CALL, A/C. CHECK THE BLOWER MOTOR. THE BLOWER WAS NOT SPINNING. REPLACED THE BLOWER MOTOR. CHECK THE THERMOSTAT, CHECK FREON LEVELS, CHECK AIR FLOW. MADE SURE THE WORK AREA WAS CLEAN WHEN JOB WAS FINISHED. EVERYTHING IS RUNNING GREAT.
CAME OUT AND INSTALLED 3.5XX H/AH TRANSITIONS AND ENLARGE RETURNS FIN THRU AP. MADE SURE EQUIPMENT WAS INSTALLED PROPERLY. MADE SURE WORK AREA WAS CLEAN WHEN FINISH. CHECK AIR FLOW, CHECK ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GREAT.
REPLACED BAD BLOWER MOTOR, CHECK CONDENSOR COIL, CHECK THERMOSTAT, CHECK AIR FLOW ALL ELECTRICAL CONNECTIONS EVERYTHING IS RUNNING GREAT.
Renewed SA, check and clean A/C, cleaned coil, adjust blower lubricated moving parts. Installed UV, everything running great.
Clean &Check A/C 6-years check con. board 2 NEW SA
clean & check a/c 6-years check the control board 2
Checked ducts for build up, cleaned condensation drain, no repairs needed.
Best HVAC work in Ashville, Al. No repairs needed.
Checked ducts for build up, cleaned condensation drain, checked ducts. No repairs needed.
Service work performed for the Heil air conditioning unit with Zep con-coil cleaner checked ducts for build up, cleaned condensation drain.
Safety check completed for the Heil air conditioning unit with Zep con-coil cleaner lubricated moving parts and checked the thermostat for wear. Best heating and cooling company in Ashville, Al
Service work performed for the Heil air condensing unit with Zep con-coil cleaner. No repairs needed.
Performed regular maintenance of the 2011 air condensing unit with heat pump. tune-up complete
All electrical connections checked for the 2012 Heil unit. Checked fan controls and manifold gas pressure