Devin j he was very professional he replace the blue light and did what he had to do when he got thru he came back in he finished the paper work I signed the paper he have me a copy.He said thank you. And he if we needed anything to call the office. Devin said have a good day. Toni
He was polite, professional and was not trying to make me buy stuff. He let me know what was wrong and fixed it. He also told me about any future issues.
top notch service - Jeremy is my preferred tech but all that I have had contact with have been very professional.My second heat pump install with Perfect Service and thus far has been a favorable experience.
Did an AC repair on a Ruud unit in Fultondale AL Checked the compressor
Did a heat repair on a 5yr old Lennox system in Fultondale AL Checked all safety controls
Did a Heating maintenance check-up in Fultondale Al on a 2-year Trane unit. Package unit heat repair Clean and check burners and burner operation.
Did an AC maintenance tune-up in Fultondale Al on a 12-year York unit. Clean and check condenser coil. The capacitor had to be replaced.
Did an HT maintenance tune-up in Fultondale Al on a 5 year Rheem unit. Check heat exchanger, fan control, and adjust blower components.
Did an HT maintenance check-up in Fultondale Al on a 19 year York unit. Check all electrical connections.
1ST MAINTENANCE CHECK-UP PER SERVICE AGREEMENT FOR 3 YEAR HEATING UNIT. CLEAN AND CHECK BURNERS AND BURNER OPERATION. LUBRICATE ALL NECESSARY MOVING PARTS, AND ADJUST BLOWER COMPONENTS. CHECK MANIFOLD GAS PRESSURE AND FOR PROPER VENTING. CHECK THERMOSTAT, FAN CONTROL, HIGH LIMIT CONTROL, HEAT EXCHANGER, AIR FILTER, AIRFLOW, ENERGY CONSUMPTION, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS OPERATING GREAT.
MAINTENANCE TUNE-UP FOR 10 YR A/C UNIT. REPLACE CAP UNDER WARRANTY. CHECK VOLTAGE AND AMPERAGE. CLEAN AND CHECK CONDENSER COIL. ADJUST BLOWER COMPONENTS, AND LUBRICATE ALL NECESSARY MOVING PARTS. CHECK THERMOSTAT, FREON LEVELS, DRAINAGE, AIR FILTER, AIRFLOW, ENERGY CONSUMPTION, COMPRESSOR DELAY SAFETY CONTROLS, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK HT. CHECK THERMOSTAT, CHECK HEAT EXCHANGER, CHECK BURNERS AND BURNER OPERATION, CHECK HIGH LIMIT CONTROL, CHECK AIR FILTER, CHECK GAS PRESSURE AND FOR PROPER VENTING, CHECK ALL ELECTRICAL CONNECTIONS, CHECK HUMIDIFIER. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING IS RUNNING GREAT.
Checked ducts for build up cleaned condensation drain with Zep con-coil cleaner, no repairs needed.
Service work performed for the Heil 2011 air conditioning unit with the pump.
Service work performed for the Heil 2017 air condensing unit with Zep con-coil cleaner. Best heating and cooling in Fultondale.
installed 2017 perfect service heat pump and air handler.
Winter heat maintenance for Birmingham Alabama customer with an 11-year-old Ruud. Check air handles control to assure the unit turns on and off as desired.