CAME OUT ON A SERVICE CALL A/C. INSTALLED A AC/FURN/COIL. MADE SURE SYSTEM WAS INSTALLED PROPERLY. CHECK THERMOSTAT, CHECK VOLTAGE AND AMPERAGE ON MOTORS. ADJUST BLOWER COMPONENTS. CHECK ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GREAT.
CAME OUT ON SERVICE CALL A/C. FOUND LEAKS AT COND.EVAP, SVC VALES AND SOLDER JOINT. INSTALLED A 3.5T PREMIUM HP/AH. MADE SURE SYSTEM WAS INSTALLED PROPERLY. CHECK AIR FLOW, CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GREAT.
HAD SERVICE CALL. CHECK DRAINAGE FOUND STOPPED UP FILTER DRAIN. CORRECTED THE PROBLEM. CHECK THERMOSTAT, ADJUST BLOWER COMPONENTS, CHECK AIR FILTER. AIR IS FLOWING GOOD. EVERYTHING IS RUNNING GREAT.
Checked air filters for build up, cleaned burners and checked gas lines for leaks. checked humidifier.
Checked ducts for build up. No repairs needed.
Checked ducts for build up, cleaned condensation drain, no repairs needed.
Checked thermostat for wear and tear, cleaned air filters, rewiring issues completed.
The checked gas line for leaks checked service igniter, made sure thermostat worked.
Service work performed on the Heil 2016 air conditioning unit with Zep con-coil cleaner, no repairs needed
Replaced bad capacitor found in 2010 Heil air conditioning unit with heat pump. No other repai\rs needed.
Checked ductwork for buildup. cleaned condensation drain found microbial growth around 1999 Trane air conditioning unit. no repairs needed.
Cleaned and serviced the 2013 air conditioning unit with Zep con-coil solution.
Cleaned and checked the 2014 air conditioning unit. Cleaned condenser coil and condensation drain.
cleaned and serviced 21 yr old Rheem air conditioning unit.
A customer with 20-year-old Bryant Hvac maintenance. Check high limit control and this prevents the furnace from over heating and causing possible damage to the unit. Also replaced Air purification system assuring quality air.