David was quick quiet and professional . He did a great job
Ian came to do our spring tune up at my daughter's house in Blountsville. He called me stating that the unit (which is new) has a problem which might be cleared with a $160 coil cleaning plus I need to pay for the service agreement, another $89 or so bucks. I paid both but wonder just what the warranty and service agreement covers?
The tech arrived early after my Sunday panic call. He trouble shot the system but never could determine what it had done or why. I guess I should have pulled the power and done a re-boot like a computer.
2ND CLEAN AND CHECK UNDER SERVICE AGREEMENT FOR 2 YR A/C UNIT. CHECK DRAINAGE, AND FREON LEVELS. LUBRICATE ALL NECESSARY MOVING PARTS AND ADJUST BLOWER COMPONENTS. CHECK THERMOSTAT, AIR FILTER, AIRFLOW, COMPRESSOR DELAY SAFETY CONTROLS, ENERGY CONSUMPTION, AND ALL ELECTRICAL CONNECTIONS. CLEAN AND CHECK CONDENSER COIL. CHECK VOLTAGE AND AMPERAGE ON MOTORS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK 12YR HEATING UNIT. CLEAN AND CHECK BURNERS AND BURNER OPERATION. ADJUST BLOWER COMPONENTS, AND LUBRICATE ALL NECESSARY MOVING PARTS. CHECK MANIFOLD GAS PRESSURE AND FOR PROPER VENTING. CHECK THERMOSTAT, AIR FILTER, HUMIDIFIER, HEAT EXCHANGER, HIGH LIMIT CONTROL, ENERGY CONSUMPTION, FAN CONTROL, AND ALL ELECTRICAL CONNECTIONS.
MAINT. TUNE-UP FOR HEATING SYSTEM ON 2UNITS, 5YR, AND 12YR. CHECK THERMOSTAT, AIR FILTER, AIRFLOW, HEAT EXCHANGER, HIGH LIMIT CONTROL, ENERGY CONSUMPTION, HUMIDIFIER, FAN CONTROL, HUMIDIFIER, AND ALL ELECTRICAL CONNECTIONS. CLEAN AND CHECK BURNERS AND BURNER OPERATION. LUBRICATE ALL NECESSARY MOVING PARTS, AND ADJUST BLOWER COMPONENTS. RENEWED SERVICE AGREEMENT ON BOTH UNITS.
CLEAN AND CHECK HT. CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS, CHECK HUMIDIFIER, CHECK BURNERS AND BURNER OPERATION, CHECK HEAT EXCHANGER, CHECK GAS PRESSURE AND FOR PROPER VENTING, CHECK HIGH LIMIT CONTROL, CHECK AIR FILTER. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
Checked High limit control, cleaned fan controls, checked the air filters.
Lubricated all moving parts, cleaned air filters, and checked voltage and amperage.
Checked Humidifier, cleaned air filters, checked heat exchangers for cracks, no repairs needed.
Provided service cleaning for 2012 Heil air conditioning unit with heat pump. Insured customer satisfaction before leaving the residence.
Cleaned and safety checked the Heil air condensing unit with Zep con-coil cleaner. no repairs needed.
Service work performed on 2015 Heil Air conditioning unit with Zep con-coil cleaner, no repairs needed.
Cleaned 2011 Heil heat pump compressor unit. No repairs necessary. Cleaned filters with Zeep con-coil cleaner.
cleaned and serviced 2008 air conditioning unit.
service work performed on 1997 air conditioning unit.
Clean and check on a 5-year-old York. Check heat exchanger. Heat exchangers can develop cracks with age. If they exist, there is a risk of serious illness from the toxic fumes emitted.
Check and clean for Hayden Alabama customer. Chek the safety controls to make sure the furnace shuts off when it is supposed to. Check vent pipes to make sure no carbon monoxide fumes are getting back into your home.