CAME OUT ON SERVICE CALL. INSTALLED 2T BASIC XX A/H 10YR P 5YR L. MADE SURE EQUIPMENT WAS INSTALLED CORRECTLY AND MADE SURE WORK AREA WAS CLEAN WHEN FINISH. CHECK THERMOSTAT, AIRFLOW, AIR FILTER, DRAINAGE, ENERGY CONSUMPTION, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS WORKING GREAT.
2ND MAINTENANCE TUNE-UP PER SERVICE AGREEMENT FOR 8 YR AIR CONDITION SYSTEM. RENEWED SERVICE AGREEMENT. CHECK VOLTAGE AND AMPERAGE ON MOTORS. CLEAN AND CHECK CONDENSER COIL. CHECK FREON LEVELS, DRAINAGE, ENERGY CONSUMPTION, COMPRESSOR DELAY SAFETY CONTROLS, THERMOSTAT, AIR FILTER, AIRFLOW, AND ALL ELECTRICAL CONNECTIONS. LUBRICATE ALL NECESSARY MOVING PARTS, AND ADJUST BLOWER COMPONENTS. EVERYTHIN IS RUNNING FINE.
1ST MAINT. TUNE-UP UNDER SERVICE AGREEMENT FOR 12YR HEATING SYSTEM. HAD LOTS OF PROBLEM WITH GOODMAN UNIT. CLEAN AND CHECK BURNERS AND BURNER OPERATION. LUBRICATE ALL NECESSARY MOVING PARTS AND ADJUST BLOWER COMPONENTS. CHECK MANIFOLD GAS PRESSURE AND FOR PROPER VENTING. CHECK THERMOSTAT, AIR FILTER, HUMIDIFIER, AIRFLOW, ENERGY CONSUMPTION, FAN CONTROL, AND ALL ELECTRICAL CONNECTIONS. CHECK HEAT EXCHANGER AND HIGH LIMIT CONTROL.
MAINTENANCE TUNE-UP FOR HT. CHECK AIR FILTER, THERMOSTAT, FAN CONTROL, ENERGY CONSUMPTION, HIGH LIMIT CONTROL, HEAT EXCHANGER, HUMIDIFIER, AND ALL ELECTRICAL CONNECTIONS. LUBRICATE ALL NECESSARY MOVING PARTS AND CLEAN AND CHECK BURNERS AND BURNER OPERATION. REPLACED PRESSURE SWITCH.
Cleaned air filters and checked high limit controls, no repairs needed.
Cleaned Lennox air conditioning unit with Zep con-coil solution.
Cleaned and sanitized 3 Ton 2015 Heil heat pump package unit. Checked for leaky evaporator coil and condensation line. No repair work needed
cleaned and checked 2010 package unit
Clean and check on a 5-year-old Ruud. Check the burner assembly, removing any rust and debris off the burners so gas can flow properly and efficiently.
CHRIS DID THE TUNEUP AND CLEANING ON A 3 YEAR OLD HEIL SYSTEM. THE CUSTOMER ALSO HAS A GAS FURNACE THAT WILL BE SERVICED IN THE WINTER.
DAVID MAY DID A TUNEUP AND CLEANING ON A PREPAID SERVICE AGREEMENT CUSTOMER. HE CLEANED A 4 YEAR OLD HEIL SYSTEM AND FOUND EVERYTHING TO BE IN GOOD WORKING CONDITION FOR THE SUMMER.
Air Conditioning repair. Diagnose, and repaired AC, for service plan customer on Heil Cooling System. Took system apart, found & diagnosed problem, explain problem & repair, on 16 year old HVAC system with R-22. Heating and cooling repair complete on air conditioner which will help ensure system cools properly for this residential customer. Central cooling system is now ready for spring and summer weather.
Air Conditioning service. Diagnose, clean and perform annual AC maintenance service plan on Heil Cooling System. Cleaned condenser coil, check Freon pressures, cleared drain lines, oiled necessary moving parts, on 1 year old HVAC system with R-410a. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for spring and summer weather.
cleaned and tuned up 13 year old ac system for the summer.