Very thorough in checking unit. The nicest technician.
The repairman seem to know his job and was very efficient. No complaints.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK CONDENSER COIL, CHECK AIR FILTER, CHECK AIR FLOW, CHECK FREON LEVELS, CHECK DRAINAGE, CHECK ALL ELECTRICAL CONNECTIONS. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT. RENEWED SERVICE AGREEMENT.
CLEAN AND CHECK A/C. CHECK CONDENSER COILS, CHECK DRAINAGE, CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. CHECK AIR FLOW. EVERYTHING IS RUNNING GREAT.
CALLED FOR AN ESTIMATE ON AIR AND GAS UNIT. PURCHASED A 3TON DUEL FUEL GAS PACK UNIT W/ T-STAT. MADE SURE THE SYSTEM WAS INSTALLED PROPERLY. MADE SURE THE WORK AREA WAS ALL CLEANED UP. CHECK AIR AND GAS FLOW. EVERYTHING IS WORKING GREAT.
HAD SERVICE CALL ON A/C. CHECK FREON LEVELS, CHECK CONDENSER COIL, CHECK LEAKAGE. HAD TO REPLACE THE EVAP COIL. CHECK AIR FLOW, EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK CONDENSER COIL, CHECK FREON LEVELS, ADJUST BLOWER COMPONENTS, CHECK AIR FLOW. CHECK COMPRESSOR DELAY SAFETY CONTROLS AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GREAT.
Service work performed for the Heil 2017 package unit with a heat pump.
Checked thermostat for wear, checked heat exchangers for cracks.
Customer satisfied with service work cleaned condensing coil. checked thermostat wear.
Lubricated all moving parts, checked ducts for debris.
Checked air filters for build up, cleaned condensation drain, checked thermostat. Best service work in Hueytown, Al.
Service work performed for the 2011 Heil package unit with heat pump, checked air flow in the home, tuned blower motor, best service work in Bessemer, al
Service work performed for the 2014 air conditioning unit with Zep con-coil.
Checked ducts for build up, cleaned and safety checked 2011 air conditioning unit with heat pump.
Service work completed for the Heil 2014 air condensing unit with heat pump. Checked ducts for build-up.
Cleaned burners, checked gas lines for leaks, adjusted blower motors, customer satisfied with the tune-up.